Marcus fixed the inexplicable problem. We now have AC!
Renewed our Gold Plan service contract
My appointment was for Monday and he came on Friday. I asked him to wear a mask seeing he had not had the vaccine and we are elderly.
On time and professional.
I recommend this company
2days later- all seems fine. Good job, nice people
Jake was very informative; answered all of my questions. He was the Best serviceman I've had to service my air conditioning unit!
Eric is thorough and makes sure the customer is satisfied before leaving.
Ac maintenance: Unit is a 2020 TRANE TEM6 5ton paired with a 5ton XR TRANE condenser. Unit is very clean and operating to manufacture spec. All electrical, capacitors and relays are in good shape. Refrigerant charge is 131/302 with 8 degrees of sub cooling and 13 degrees of super heat. Unit is operating at a 20 degree temperature drop with 56% humidity.
Ac maintenance on 2 split systems
Rheem 2011 Customer has dogs Ac maintenance: Indoor unit has bacterial growth in and out, recommended a uv light to help combat problem. system is running inefficiently. Recommended updating to a newer more efficient model, home owner declined. Went ahead and replaced 12.5uf capacitor on indoor blower. System is operating close to manufacture spec but needs to be updated.
Perform maintenance on ac system. Unit older but cooling properly. Find burnt out uv bulb. We need to quote bulb replacement.
Ac gold maintenance performed. York AC is operating within manufacturers specs. No surge protection present. Recommend uv system and surge to protect the system in the future.
Air conditioning service performed found a part under warranty and replaced on the spot customer is very happy that I could fix it the same day.
Ac maintenance on 2015 trane split system
Ac maintenance performed. He tech found several issues including a aux drain pan being filled with water. The evaporator coil is very rusted and freezing up. There is sitting water in the bottom of the air handler which is leaking out of the cabinet. The system is low on refrigerant. The customer asked for a quote to replace the older system with the issues.
Ac gold maintenance performed on a 2020 York split system. The air conditioning is operating properly and running at manufacturers specs. The technician strongly recommends a surge protection to protect from power surges and Mother Nature.
Ac complimentary maintenance. Older Trane system, as several little issues. The start capacitor is below manufacturers specs. Also has a biological growth problem inside the air handler. The customer declined any options at this time.