Space getting too cold found stats set to fan on instructed customer to leave fan on auto because the stat wire is bad and I had to wire the unit differently to make it cool when fan comes on
Found front fridgedaire frozen turned off unit to thaw. Found back Amana unit blower only found bad stat wire from unit to stat temporarily wired cool wire with blower wire to cool when ever fan comes on Must return to run new stat wire don’t know price ceiling is Sheetrock.... no access to wire in space
Installed uv kit with 2 yr bulb. System is operating correctly
Air-conditioning warranty service performed
….Helped Installer’s get air handler out of attic as well as installed Wi-Fi thermostat called owner and touch base with him he is going to pay online with a credit card when he gets home thank you
….sold new system scheduled for tomorrow at 8-9am
Air conditioning service performed
Air conditioning service work performed
Air-conditioning service performed found two systems with bad dual caps. Sold customer capacitors installed capacitors and sold a three system maintenance for friends and family platinum plan. Collected all amount due
HVAC MAINTENANCE DONE UNIT IS RUNNING GOOD AT THIS TIME.
Ac repair. Checked a trane air conditioning system for an oil leak. Did not find oil, found condensation and mildew on cement.