Found drain line clogged and float switch tripped Jake was just out here today.
Upon arrival all systems were running except for the New York unit was turned off. Set thermostat to cool and equipment started and ran normally. Checked over AC system. Suggested to call and schedule a maintenance. Equipment is running normally at this time. Changed the Honeywell thermostat from a non-programmable to a programmable At clients request.huhjh
Installed a warranty 8 kw heater.
Checked all the things that the inspector had on the list that had issues. Gave the customer a quote on replacement of 2.5 ton system and installing 35 feet of drain line from the 3rd floor system.