Courteous and prompt technician. Happy with the service.
Repaired a Carrier air conditioner
Looked at a Lennox air handler
Repaired a Tranefgas furnace
Fixed a Rheem heater that had a broken thermostat.
Fixed a furnace that had a wrong setting on its thermostat and a dirty filter.
Fixed a Goodman that needed a new ignitor.
Fixed an ac that had a broken blower motor.
Diagnosed a broken ecm motor that will need replacing.
No mechanical problems found
We found an evaporator with a restriction and will submit it to be replaced.
Found terminals burned off of the compressor
Installed a hard pipe kit and cleaned a flame sensor on this furnace yo fix it.
replacing a warranty control board in a Lennox heat pump
a couple of simple wiring repairs and a new transformer and this business is back up and cooling again!