Diagnosed a Carrier heatpump with a broken reversing valve.
Fixed a Carrier heater that had bad airflow.
Fixed an Allstyle coil that had a refrigerant leak.
Fixed a Carrier AC that had a blown out capacitor.
Fixed a Lennox AC that had a broken capacitor and low refrigerant.
Fixed a Tempstar AC with a blower and fan wheel.
Disgnosed a Nordyne AC that had a restriction in the evaporator of the indoor unit.
Cleared a drainline and will order a replacement motor for an AC.
Fixed an AC with corroded thermostat wires.
Fixed a Goodman that had a broken thermostat connection.
Diagnosed an AC that had a leak caused by a roofing nail.
Filled an ac with refrigerant after fixing it.
Filled an ac with refrigerant to keep it cooling for the year.
Fixed an ac that froze up from a broken fan, and found another with a grounded compressor.
Diagnosed an ac that has a leak in it's evaporator