Fixed a clogged drain on a Trane AC and replaced a broken drainpan.
Fixed a Trane AC that had a broken fan.
Diwgniaed a Trame AC with a broken fan motor.
Fixed a Trane air conditioner that had a leak in the condenser, and soldered it.
Diagnosed an AC with a leaking air handler that needs replacing.
Diagnosed a Carrier heatpump with a broken reversing valve.
Fixed a Carrier heater that had bad airflow.
Fixed an Allstyle coil that had a refrigerant leak.
Fixed a Carrier AC that had a blown out capacitor.
Fixed a Lennox AC that had a broken capacitor and low refrigerant.
Fixed a Tempstar AC with a blower and fan wheel.
Disgnosed a Nordyne AC that had a restriction in the evaporator of the indoor unit.
Cleared a drainline and will order a replacement motor for an AC.
Fixed an AC with corroded thermostat wires.
Fixed a Goodman that had a broken thermostat connection.