Service was excellent
Venny was very polite and knew what he was talking about. He was fast but efficient. Even though my mom was asking a million and one questions and some of them the same questions he was still very polite and answered her. Definitely would recommend him and his company to others!
I appreciated that they narrowed down an appointment time, gave me 30 min warning that they were on their way and showed up on time. Rigo was knowlegable and helpful in troubleshooting my problem. Turns out my coils were freezing over because I wasn't changing out my air filter, so the frozen over coils were blocking the airflow. They were thawed out by the time the tech arrived, so we were good to go. I thought the pricing kind of steep. $99 to inspect my equipment and tell me my coils froze over just seems (OUCH!) high. $35/hr would have been fair. Still, I'm grateful for the peace of mind. It really sucks when your house is hot and humid.
Performed maintenance on a Goodman furnace.
Fixed a Payne brand heater that had a broken thermostat.
Fixed a Carrier AC that had a broken capacitor.
Fixed a Lennox AC that had a backef up drain.
Fixed an ICP air conditioner that had a clogged drain.
Fixed a Carrier AC that was tripping its circuit breaker.
Fixed a York compressor with a terminal repair kit.
Fixed a Payne brand AC that had a clog.
Found an AC with a clogged drain in the main plumbing.
Diagnosed a Lennox AC that had a bad compressor.
Diagnosed an AC with a bad compressor locking up.
Fixed an AC that needed a capacitor.
Cleared out a drainline and found an AC with a cracked pan that needs replacing.
Checked some ductwork on a Goodman AC.
Fixed a Carrier that had a blown capacitor.