Service was excellent
Venny was very polite and knew what he was talking about. He was fast but efficient. Even though my mom was asking a million and one questions and some of them the same questions he was still very polite and answered her. Definitely would recommend him and his company to others!
I appreciated that they narrowed down an appointment time, gave me 30 min warning that they were on their way and showed up on time. Rigo was knowlegable and helpful in troubleshooting my problem. Turns out my coils were freezing over because I wasn't changing out my air filter, so the frozen over coils were blocking the airflow. They were thawed out by the time the tech arrived, so we were good to go. I thought the pricing kind of steep. $99 to inspect my equipment and tell me my coils froze over just seems (OUCH!) high. $35/hr would have been fair. Still, I'm grateful for the peace of mind. It really sucks when your house is hot and humid.
Repaired s Bryant heat pump
Replaced inducer assembly for rheem furnace
Fixed a Goodman furnace that had dirty burners not igniting good.
Changing filter for a First Co airhandler
Working on a ruud furnace. Inducer is locked up
Fixed a General Electruc heater that had a bad heatstrip.
Diagnosed a broken heatstrip on a fir down.
Control board was bad
Fixed a Comfortmaker furnace that had a broken thermostat.
Tuned up a Rheem furnace and checked for gas leaks.
Replaced gas valve for rheem furnace
Fixed a Goodman fir down that had a blown fuse.
Installed low voltage conduit