Service was excellent
Venny was very polite and knew what he was talking about. He was fast but efficient. Even though my mom was asking a million and one questions and some of them the same questions he was still very polite and answered her. Definitely would recommend him and his company to others!
I appreciated that they narrowed down an appointment time, gave me 30 min warning that they were on their way and showed up on time. Rigo was knowlegable and helpful in troubleshooting my problem. Turns out my coils were freezing over because I wasn't changing out my air filter, so the frozen over coils were blocking the airflow. They were thawed out by the time the tech arrived, so we were good to go. I thought the pricing kind of steep. $99 to inspect my equipment and tell me my coils froze over just seems (OUCH!) high. $35/hr would have been fair. Still, I'm grateful for the peace of mind. It really sucks when your house is hot and humid.
Fixed a Goodman AC that had a melted capacitor, but found a melted breaker that will need an electrician.
Fixed a Goodman heater that had a brooen thermostat.
Fixed a Goodman unit that had a burned out breaker.
Fixed a Goodman heater that had a melted breaker.
Fixed a Nordyne furnace that had a broken ignitor.
Fixed a Lexaire furnace that was blowing cold air.
Fixed a First Company brand heater that had a bad heatkit.
Fixed a Carrier heat pump that had a loose door on it.
Fixed a Goodman furnace that wasn't turning on.
Diagnosed a Trane AC with a grounded compressor.
Performed maintenance on a Goodman furnace.
Fixed a Payne brand heater that had a broken thermostat.
Fixed a Carrier AC that had a broken capacitor.
Fixed a Lennox AC that had a backef up drain.
Fixed an ICP air conditioner that had a clogged drain.