Service was excellent
Venny was very polite and knew what he was talking about. He was fast but efficient. Even though my mom was asking a million and one questions and some of them the same questions he was still very polite and answered her. Definitely would recommend him and his company to others!
I appreciated that they narrowed down an appointment time, gave me 30 min warning that they were on their way and showed up on time. Rigo was knowlegable and helpful in troubleshooting my problem. Turns out my coils were freezing over because I wasn't changing out my air filter, so the frozen over coils were blocking the airflow. They were thawed out by the time the tech arrived, so we were good to go. I thought the pricing kind of steep. $99 to inspect my equipment and tell me my coils froze over just seems (OUCH!) high. $35/hr would have been fair. Still, I'm grateful for the peace of mind. It really sucks when your house is hot and humid.
Fixed a Trane furnace that had a bad pressure switch.
Cleared clogged drain line
40 plus year unit finally gave out.
Removed dirty filter from trane system
Completed mtc on a goodman furnace
Fixed a Carrier AC that had a broken capacitor and start kit.
We do gas furnace repair also
We work pretty much all over dallas metro
Fixed a Lennox AC that had ants stuck in a contactor.
Found a clogged drainline that will need a plumber.
Fixed a clogged drain on a Goodman AC.
Fixed a broken AC by replacing the fan motor.
Fixed a Goodman AC with a leakseal.
Fixed a Trane AC that had a broken capacitor.
Fixed a Trane air conditioner with a broken capacitor.