Diagnosed a Carrier AC with a leaky evaporator.
Fixed a Goodman heater that had a busted control.
Fixed a furnace that had a dirty sensor.
Fixed a Carrier furnace that had a loose control board connection.
Fixed a York furnace that had a broken thermostat.
Tuned up a pair of Goodman furnaces.
Cleared a clog in a Goodman AC.
Fixed a Lennox that needed new capacitors.
Fixed a Goodman AC that had a broken capacitor and tripped breaker.
Fixed a Goodman AC that had a broken capacitor.
Fixed a Lennox AC that had a melted wire.
Fixed an AC that had a broken disconnect.
Fixed a York AC that had a broken capacitor.
Diagnosed an AC that had a broken blower wheel.
Fixed an AC that had a bad control board and capacitor.