Fixed a zoning system AC that had a loose wire on a damper.
Fixed a Goodman AC that had a bad float switch.
Fixed a Carrier AC that had a broken thermostat.
Did an AC maintenance and recommended more return air on a system.
Tuned up a Trane AC that needed cleaning.
Fixed a Carrier AC that had a broken capacitor.
Tuned up a furnace and made sure it had no problems.
Replaced a big emergency drain pan under an AC and furnace in an attic.
Fixed a Nordyne AC that had a broken 2 speed fan.
Diagnosed a broken condenser fan motor on a Nordyne AC.
Diagnosed a Lennox AC with a leak.
Fixed a Payne air conditioner that had a leak.
Diagnosed an AC that had a leak in its copper lineset.
Tuned up a Lennox furnace for the winter.
Tuned up a Carrier brand furnace.