Diagnosed an AC that had a leak in its copper lineset.
Tuned up a Lennox furnace for the winter.
Tuned up a Carrier brand furnace.
Fixed a York AC that had a clogged drain.
Fixed a Carrier AC that had uninsulated lineset dripping condensation.
Fixed a Lennox AC that had a broken capacitor.
Checked an AC that has an intermittent problem we will need to catch another time.
Replaced a broken cap on a Lennox air conditioner.
Showed a customer how to change the filters in a Lennox furnace.
Fixed a Carrier unit that had a blown out capacitor.
Fixed an old York AC that had low refrigerant.
Fixed a Goodman AC that had a clog.
Fixed another Carrier AC that had a bad capacitor.
Fixed a Trane AC that had a tripped breaker.
Replaced a broken capacitor on a Carrier AC.