Gabriel was awesome! He diagnosed the problem and was able to fix it the same day. So happy to have a cool house again!
Wow best a/c company I’ve ever dealt with. They responded quickly and were very professional!
Gabriel was very informative and professional. He looked over the entire system and repaired/ replaced the defective item.
Michael was very quick and answered all my questions. Every knowledgeable and efficient.
The young man who came to fix my thermostat was excellent finished quickly he was professional polite and explained the operation of the new thermostat so that I knew how to regulate the temperature
Great service. MIchael was polite and knowledgeable. He showed me the broken part and took the time to explain it. I would recommend Michael and ac wizard for future work.
Was able to detect an issue with the upstairs sink. Installed two float switches for future safety.
Performed fall maintenance on two Carrier Furnaces. Both units are producing a good delta T and there are no issues.
Fixed a Goodman AC that had a clogged drainline.
Fixed a York furnace that had a broken ignitor.
Cleared primary and secondary lines and added a hanging kit to ensure proper drainage.
Fixed a Goodman AC that needed a drainline cleared.
Fixed a Trane AC that needed a start kit to stop a compressor from melting wires.
Fixed a Goodman AC that needed a capacitor.
Diagnosed a leaking Lennox air conditioner.
Diagnosed a Goodman AC with uneven cooling across the house.
The compressor was off upon arrival and no refrigerant was passing through the liquid line. Replaced run cap and checked the pressures. The unit is now cooling and there are no other mechanical issues at this time!
Replaced an 80 microfarad capacitor. Temp difference between the supply plenum and the return was between 15-17 degrees. The house is cooling and at this time there are no other issues.
Replaced control board and the temp difference is around 20 degrees. The house is cooling!
Dual run cap had gone bad so we replaced it with a new one. Checked the amps on compressor and fan motor and everything looks good. Temp difference is where we need to be. System is running and cooling again!
Cleared a clog in a drainline on an AC.