He was pleasant and explained things clearly and was knowledgeable
Fixed a broken Trane furnace with a control board.
Fixed a Carrier furnace that had a broken thermostat.
Fixed a York furnace that had a broken sensor.
Cleaned a dirty sensor on a Trane furnace.
Performed maintenance on a Bryant furnace in Sachse.
Fixed a Lennox AC that had a broken start kit.
Fixed an Amana AC that had a broken capacitor.
Diagnosed a Carrier AC with a leaky evaporator.
Fixed a Lennox AC with a new fan motor.
Diagnosed an old Carrier AC with a broken compressor.
Fixed a York AC that had a leak on the cieling.
Fixed a drain on an AC that was clogged.
Fixed a Lennox AC that had a broken fan.
Fixed an Amana AC that had dirty filters.
Tuned up a Bryant AC and replaced a weak capacitor that was going to break soon.