Gabriel was very professional and diagnosed the problem very quickly. He deserves a raise!
It was good service, just sad that I lost $75.
The service was professional
He was efficient, professional and fast.
They provided service for heater fan issue. Their system is great with clear communication. The technician was very professional and knew what he was doing.
Tstat not sending signal to hear pump changed out tstat no other issues found
Fixed a Trane heater that had a melted circuit breaker.
Fixed a Carrier furnace that had a melted heatkit.
Diagnosed a broken heatkit in an air handler.
Replaced a bad damper motor on a Lennox heater.
Fixed a Carrier brand furnace that had a broken control board under warranty.
Fixed a Nordyne furnace that had loose wiring to the zoning board.
Diagnosed a bad pair of circuit breakers inside a trane air handler.
Diagnosed a broken control board in a Carrier unit.
Fixed a Carrier furnace that had a dirty filter.
Fixed a Goodman heatpump that had a broken capacitor.
Diagnosed a broken damper motor on a Lennox zoning heatpump.
Fixed a Trane air handler heater that had a broken blower.
Replaced cfm for trane heat pump
Fixed a Carrier furnace that had a broken pressure switch.