Michael was able to correct the issue.
Gabriel was very professional and diagnosed the problem very quickly. He deserves a raise!
It was good service, just sad that I lost $75.
The service was professional
He was efficient, professional and fast.
They provided service for heater fan issue. Their system is great with clear communication. The technician was very professional and knew what he was doing.
Performed fall maintenance on a Trane air handler. All heating components are working and the filter is clean!
Cleared out drain lines for the ac units. Units are draining properly.
Found a leak in the evaporator coil. We will need to submit it in to American Home Shield for a replacement.
Fixed a zoning AC that had a broken damper.
Unit’s contactor was faulty. Replaced the contactor and checked pressures. The Freon levels looks good. Unit is running as normal.
Fixed a Carrier AC that had a broken control board.
Checked on unit. Will need to check back when it gets hotter.
Changed out bad run cap
Ran new tstat wire
Changed out broken fan blade and disconnect
Evap coil replacement
Refrigerant needs oil
Diagnosed a broken compressor on a Trane air conditioner.
Replaced blown start kit for trane heat pump