Very informative about what I need to do.
Very polite and thorough.
What super nice guy. The kind of person you feel so comfortable with that if you had to leave him alone in your hom you could do it. He also was no pressure, polite an clean cut looking. He put a sticker on my furnace an I definitely plan on using your company if I need any repairs. Thanks again, James Barrett an Access Heating Barbara Shearet Boise
Brandon made sure I understood everything he was doing and showed me what needed fixed and why.
did not do a full cleaning job
John was very professional and prompt...answered all my questions very well.
Quick, friendly, fast and a job done well!
thank you he was working fast and got the job done thank you.
Reviewed settings in thermostat. Reviewing with Aaron. Pictures stored in file.
Check system and found furnace not igniting. Checked igniter probe all is operating properly but was not set in flame properly to ignite. Readjust igniter and cycled on several times all is working good at this time.
Did the pictures and measurements for the free furnace contest.
Checked water heater operation found pilot light would not stay lit. Checked valve and controls found gas valve not working properly. Replaced gas valve, system cycled on good and is working properly. Also performed maintenance and flush on water heater. Found water connection leaking, tightened all water flex connections and is good and leak free at this time. Also found expansion tank defective, diaphragm in tank has been ruptured and needs to be replaced. Replaced expansion tank and pressurized it to 70 psi per house pressure and is operating good.
Did pictures and measurements of the furnace for the contest
Completed entry into the free furnace contest with the pictures and measurements. System age is 2002-2003
Free furnace entry invoice, the furnace is a 1992 up flow in the basement, this is a Lennox Pulse furnace this serial number is possibly under the old expired Recall they had in the late to mid 90â€™s.
Checked system operation found combustion inducer assembly motor has excess of end play and causing the motor to rattle. Also performed overview of heating system and found secondary heat exchanger has a major hole and is leaking condensation Onto the primary heat exchanger and resting the chamber out very badly. Shut system down due to unsafe conditions and improper functioning of combustion. Heating system can be repaired but with that age and cost of repair, replacement may be a better option.
Input all system information in for the free furnace contest.
Completed ac maintenance. System is working properly at this time.
Input of all pictures and measurements for the free furnace contest
Input furnace contest information
Completed system inspection. Found system working properly at this time. Noticed system has some signs of wear due to age, dirty blower wheel, and fraying thermostat wire at the condensing unit. But system is operating properly at this time.
Entered information for furnace contest
Completed entry into free furnace contest