Air Force One arrived on time, completed the project in good time, explained the process, and charged me a fair price. I can’t recommend them enough!
Response from Air Force One Plumbing, Heating & Air:
Thank you for giving us five stars We look forward to helping you out in the future!
Always know that our heat and air are being taken care of by a PRO! Thank you for consistently giving us great service!
We have been using Air Force One for years because they are honest & reliable. We feel very lucky to have Dale R as the technician they send out. He is always prompt & professional.
Kevin came out on time and quickly checked all the possibilities of why my AC unit wasn't coming on. It turned out to be just a loose wire in my thermostat, so he fixed that. He also gave me some advice on replacing my old condenser and coil, which is on my list of improvements to my home.
This company provides a great service & they are honest!!
Technician came out on Thursday, November 13th. He informed us that we needed a new furnace and he would have us an estimate either later that day or the next day. When I had not heard anything by Tuesday morning I called the office and they said they would see what happened and get back to me shortly. I still have not heard anything so I assume Air Force One is not interested in my business. I will have to proceed with another company.
Merit Series, Upflow/Horizontal Gas Furnace, 80% AFUE, 88,000 Btuh, Power Saver Constant Torque, 1 Stage, 3-5 Ton, ML180UH090E60C
Returning on Monday to replace Unit
Clean flame sensor system is working as usual
Sending quotes for ecobee thermostats and sensors and one return duct.
Replaced this improperly installed garbage disposal that was leaking and constantly clogging.
Reset limit switch on a york furnace and installed a honeywell thermostat
Maintenance check up two systems prepaid both systems are working great..
Replaced gas valve on trane furnace . checked furnace all working properly.
Heating Check of one trane system. Replaced filter 16x25x1. Tested for carbon monoxide, tested safeties ok. Checked motor amps, capacitor and electrical. Checked thermostat operation, working. System is operating safely and efficiently.
Blew out TNstopped up drain with compressed air.
Found system low on r22 frwon, added 3lbs of r22 and super seal to downstairs system
Heating tune up of one rheem furnace. Filter was clean, 16x25x4. Cleaned flame sensor, tested safeties, cleaned the flame sensor. Found no carbon monoxide leaks and the furnace was burning properly.
Call back from after hours service call found the low voltage fuse blown. low voltage wire going outside shorting out fuse will need to be replaced. Also found week outdoor capacitor and 1 l_b_s low of R22 freon customer will clean condenser coils outside every filter change ....tech will return saturday to run new thermostat wire to the outside
Found capacitor on carrier condenser readin 0 mfd and leaking. Also needs fan blade replaced, has a crack in it.
Found outside condenser clogged with Cottonwood water washed coils checked refrigerant levels normal all working fine