Explained a lot about the system to us. Was kind enough to install a filler before he left.
I am a happy camper
Spring Residential Air Conditioning Maintenance. Compressor starting amps right at specified limit highly recommend hard start kit to prolong the life of compressor other than that the system is running and cooling as designed.
System is working properly at this time no issues were present
Perform system maintenance ensured system was working to manufacturer specifications talk to the customer about the value of continuing maintenance customer filter size is 16 by 25 by 4 see attach pictures for more details
2 system full system PM. Checked system in cool and heat. Checked temperature differentials. Checked electrical components. No issues found at this time. System is working as designed.
power disconnected to furnace System came back on when replied in addition to gas pressure for manifold is sky high will reconvene on later date to adjust See attached video
Found leak in evaporator coils and charged system with 8 lbs of 410a, needs replacement warranty coils.
Blew out main drain line with compressed air
Technician Ricardo reported to a after hours call found outside condenser coil stopped up needing to be water washed a defective kickstart or starter kit for the compressor and the system was low four pounds of r22 refrigerant found shut off valves leaking needed to open and close until they stop leaking and added we clock to the threads and tighten down the caps after all repairs refrigerant levels checked normal temperature dropped 20 degrees inside system is ready for a hot summer
Heating check of one trane furnace, replaced blower motor capacitor