Springtime Thermostat Repair for a residential customer near Oran Good Park. Found thermostat to be semi functional. Replaced and confirmed function found C wire to not be sending 24v recommend replacing low voltage wire follow up.
Springtime Air Conditioning Maintenance for a residential customer near Webb Chapel Road. Inspected units for cooling, replaced all air filters and found condenser 3 to have a low capacitance run capacitor recommend replacement.
Spring Air Conditioning Installation for a commercial customer. Installation of a Trane 2 stage control board. Installed board and tested function system running as designed. Invoice pay link emailed to Amanda contact she said she will get it paid this morning once done on the phone.
Spring Residential Air Conditioning Repair Service. The technician arrived and found that the back right a/c unit was not running. The technician climbed onto the roof and ran a diagnostic of the unit. High voltage power was found to be working. Low voltage was found to be functioning at the transformer. 24 volts were found on R but no voltage was found on G. Board was not sending 24 volts to the contactor and therefore not engaging high voltage. The technician will need to contact tech support to confirm whether the board or thermostat is the cause of failure. A follow-up call will be scheduled ASAP. The thermostat was found to be functional however board was not sending out a command signal when prompted. Until a separate diagnostic board was used the system ran as designed. Board ordered will follow up with the customer when it arrives.
Install matching Goodman 16 SEER Condenser and Coil with 10 Year Parts Labor and Refrigerant Warranty
Heater not working
Replace drains as is, with single drain run to roof drain with condensate stands every 5 ft.
Indoor fan blower motor had to be rewired properly. Outside unit boardd and fan motor were both inop once replaced everything ran fine. Customer said parents will call to pay tomorrow.
Giving the customer a quote to replace 80 feet of 3/4 inch PVC as well as struts and correctly Pitch the drains
Installed 3 ton 410a tempstar rooftop package unit
Added 2 pounds r22 with sealnt for better cooling on trane 4ton system.
Technician Ricardo and Antonio found Rheem gas pack rooftop cooling system coil suffering from dirty sock syndrome will need to give prices on a cleaning solution