Great job as always. Very professional and thorough. It’s why I continue to use AFO for these past 10+ Years.
he was great will use again
Response from Air Force One Plumbing, Heating & Air:
Glad to hear it. Thanks for the review
I just renewed service for another year. Service and price must be good for me to keep coming back.
We were in need of a check up and gave Air Force One a call. They were here quick and Kevin did a great job as always.
Professional service. Prompt response when called to handle a breakdown.Cost competitive.
Great company, honest, timely, professional, friendly. Just few words for a company with a long history of quality service.
Outdoor unit was not running. Capacitor was blown. Replaced capacitor and tested unit. It is working properly at this time.
Will reconvene on Monday
Technicians found garbage disposal was working but was making a loud noise. Technician removed disposal and cleared food debris under the blades that had accumulated. Rotors were lubricated and tested. Disinfectant was sprayed to remove smell and garbage disposal was reattached. The motor was checked and amperage was on the upper end of acceptable. Due to the age of the unit (04/2011) the system is showing normal wear and tear.
Formed system maintenance talk to the customer about float switches Customer has already declined previously no further recommendations at this time
Found unit Clog
5 Ton up to 16 SEER Condenser and Coil
Found outside condenser tripping breaker on the inside recommended condenser evaporator coil replacement customer agrees will be returning later this week to install both
Sending the customer quote for replacement as well as repair
Capped a froze water line in the garage that was leaking due to the hard freeze. Will return to repair at a later date.
Perform system maintenance insurance system is working within manufacturer specifications talk to the customer about the downstairs system having issues With outside condenser coil disintegrating
Replaced segment of 1/2â€ copper line which was removed and capped due to leak. New pex line was installed and tested. No leak present and all fixtures are working.
16 SEER Two Stage American Standard Gas Furnace
Returning on Wednesday at 8 to install new furnace
Flipped Breaker will revisit on Friday to further diagnose
1 system spring PM. Checked blower motor amps. Checked temperature differential. Inspected coil and duct work. Checked condensing unit. Coils are clean. No issues found at this time. System is ready for summer weather.