Great job as always. Very professional and thorough. It’s why I continue to use AFO for these past 10+ Years.
he was great will use again
Response from Air Force One Plumbing, Heating & Air:
Glad to hear it. Thanks for the review
I just renewed service for another year. Service and price must be good for me to keep coming back.
We were in need of a check up and gave Air Force One a call. They were here quick and Kevin did a great job as always.
Professional service. Prompt response when called to handle a breakdown.Cost competitive.
Great company, honest, timely, professional, friendly. Just few words for a company with a long history of quality service.
System is performing too manufacturer specifications Warranty
Customerâ€™s water heater pilot was not on. Technician lit pilot to water heater and water heater is currently working.
5 Ton 14 SEER American Standard Gas Full System Installation
3 Ton and 4 Ton 16 SEER Two Stage Complete System Installation.
Technician arrived with electrician who photographed and diagnosed faulty and intermittent power at the disconnect. Electrician was able to restore constant 240 volts to upstairs unit. The dual run capacitor was replaced with a new 45+5 capacitor and system was started. System is currently running and customer will monitor if system is able to cool properly and will call back with an update.
Compressor was found to not be running. Run capacitor had blown all its oil and the wiring in the compressor probably failed at the same time. Power surge suspected
Replaced indoor fan motor for upstairs unit
Change fan motor assembly on outside downstairs unit as well as filled up charge on both systems we will be back in the fall to check on system health again. told the customer about probability of future problems due to the age of system
Technician removed existing garbage disposal and replaced it with exact same make and model. Garbage disposal was tested and no leaks present and system is working as intended.
Refrigerant left reclaimed and replaced. Additional refrigerant added to make up for what was lost from leak. Coil replaced under parts and labor warranty. Coils acid washed and filter drier replaced.
Upon arrival found bad outside capacitor System is working properly at this time
Returning to replace coil customer will call and schedule
Completed system maintenance everything is working properly at this time please see pictures attached
3.5 Ton 14 SEER American Standard Single Stage Gas System
Sending estimates for replacement on Monday