Great job as always. Very professional and thorough. It’s why I continue to use AFO for these past 10+ Years.
he was great will use again
Response from Air Force One Plumbing, Heating & Air:
Glad to hear it. Thanks for the review
I just renewed service for another year. Service and price must be good for me to keep coming back.
We were in need of a check up and gave Air Force One a call. They were here quick and Kevin did a great job as always.
Professional service. Prompt response when called to handle a breakdown.Cost competitive.
Great company, honest, timely, professional, friendly. Just few words for a company with a long history of quality service.
AC Repair for a residential customer near Centennial High School. Line is not clogged according to tenant it backs up in the heat of the day indicating the line is not draining efficiently. Recommend rerunning the line to a condensate pump then into the attic and out of the eve of the roof down to the ground.
3lb 30z of 410a and leak seal dye pack installed under warranty. Scheduledfollow up leak check.
Checked system found no deficits or issues at this time
Inspected units for cooling only minor concern was both systems compressor starting amps were higher than the LRA tag allows for. Recommend hard start kits to help increase longevity of the system by taking some of the work load off the compressor on start up.
No uv signature detected anywhere in the refrigerant circuit. Customer will calll if unit stops cooling or we will recheck at their next maintenance.
Spring Air Conditioning Maintenance for a residential homeowner. Inspected unit for cooling. No issues found other than compressor pulls high amperage on start up. Recommended adding hard start kit to prolong compressor life span. Customer satisfied on departure.
Air Conditioning Repair for a residential homeowner having cooling issues. Technician sent to diagnose. Refrigerant leak -1lb 10oz 410a and 1 UV dye pack. Scheduled follow-up leak check.
Air Conditioning repair for a residential homeowner. Technician arrived and photographed damage to ceiling and introduced customer to sheet rock repair specialist. Sheetrock repair will begin at 8:30 on 3/29 with tech following up to ensure customer satisfaction. Tech also reviewed findings of PCM and will provide customer with options for refrigerant leak searches via email.
HVAC Repair for a residential customer. Inspected units both for cooling. Found upstairs unit to only have a temperature split of 9.5 instead of the standard 17-22. Subcool on same system is also only 4.5 indicating it is low on refrigerant which also indicates a potential leak in the refrigerant line. The down stairs unit furnace and condenser both performing to standard except the existing hard start kit is not functioning and needs replaced which is causing unit compressor to pull high amp draw on start up. Customer would like a quote on a replacement system for her 2.5ton 16seer system.
Furnace Maintenance - Inspecting furnace for heating, and replacing filter. Customer renewed their maintenance membership.
System is performing too manufacturer specifications Warranty
Customerâ€™s water heater pilot was not on. Technician lit pilot to water heater and water heater is currently working.
5 Ton 14 SEER American Standard Gas Full System Installation
3 Ton and 4 Ton 16 SEER Two Stage Complete System Installation.
Technician arrived with electrician who photographed and diagnosed faulty and intermittent power at the disconnect. Electrician was able to restore constant 240 volts to upstairs unit. The dual run capacitor was replaced with a new 45+5 capacitor and system was started. System is currently running and customer will monitor if system is able to cool properly and will call back with an update.