We replaced our heat/air conditioning about 4 months ago and our home was comfortable through the frigid temperatures of the storm last week, a couple of rooms were even too warm! They came out and added dampers and adjusted the air flow. The service has always been prompt, courteous and friendly. Thanks.
This was a routine maintenance and done on time and positively!
Rick came out and had my compressor back up and running quickly. He is always thorough and diagnoses the problem easily. He is polite and friendly and cleans up after himself. He is a valuable asset to any HVAC company. Thanks Rick for an awesome job!
Ya'll are awesome for coming so fast on a Saturday and Rick was great. Thank you!
I've used Air Force One Air Conditioning several times now and every time I've used them they've done a good job. Rick came out and diagnosed my problems quickly and had it repaired quickly. He didn't mind my questions and happily explained what I wanted to know. They have good customer service and their techs are knowledgeable. Pricing is a bit high but that's the case no matter who you call out for AC work.
Dale was very courteous and professional. He thoroughly checked my heating systems to make sure they were working properly.
Called Samsung Tech Support diagnose to bad motherboards will reconvene on Friday motherboards location at shere in Allen
Replace water servo with new special ordered replacement.
system maintenance found both systems to have leaks that did not improve since the last time we spoke recommend evaporator coil replacement on both units as well as condenser coil to rectify issue in prevent breakdowns in the middle of summer
Technicians arrived and found water heater not functioning. Water valve was opened and leak was found at water servo. An estimate for replacing the water will be provided to customer and will call back to confirm installation date.
Installation of tankless unit
Found o-ring in water control valve worn and damaged. Replaced damage o-ring. Small crack detected in plastic of water control valve. Attempted to repair with epoxy
Installed 8â€ and 9â€ dampers. Blowing less air to affected rooms. Customer is content with dampers being open half way. 2 system PCM. Checked blower motor amps. Checked inducer motor amps. Inspected duct work. Replaced air filter. Cleaned flame sensor. Checked electrical components. Checked mini split unit. Left side room is not keeping up. Room has 4 windows all facing sun and heat from downstairs unit is keeping room hot. Advised customer to leave system on cool and allow unit to drop temperature. Right side split is working fine. Noticeable temperature difference between the two rooms.
2 system winter check. Both systems were installed less than a year ago. No issues found at this time. Systems are working as designed.
Added 3 lbs of r22 to lennox system
Found defective blower wheel on furnace will need to be replaced I'll show emergency drain pans rested needs to be replaced will send out bid on replacement on 5 ton system
Cooling Check of 2 carrier systems. Replaced 3 capacitors, added celing saver to one system, replaced one voltage controller and added 2 compressor savers. Water waahed condenser coils, ch ecked freon levels.
Technician Ricardo was out in McKinney working on a dream conventional gas heat air conditioning system found miss wired capacitor sticking contactor dirty evap coil and blower and a week blower capacitor recommending using pleated filters once wiring and contactor was replaced refrigerant levels checked normal no other issues were found system is ready for
Technician Ricardo found outdoor capacitor bad causing compressor not to turn on had to also add a Start Kit with new capacitor compressor seems to be getting weaker but now after replacing defective part and adding the Start Assist system is operating normal now refrigerant levels checked out normal temperature drop across the indoor air handler 18 degrees other than that no other issues were found ready for a hot summer
Technician ricardo arrived at a call back Saturday found outside condenser motor locked bearings going out very hard to turn system tripped on high pressure safety switch will need to find out if system is under warranty Monday if not we'll need to charge or the motor and evap coil that is leaking other than that system is operating normal now we thank you for your business
Technician Rick diagnosed outside unit not coming on due to 1 pole contactor defective causing only 115 volts out of 240 through replaced defective contactor check refrigerant charge recommended washing outdoor unit every month or two other than that refrigerant level checked fine no other issues at this time awesome people thank you for the eggs that's pretty cool we thank you for your business your system should be ready for a hot summer