Have used their service for three years and it's always easy to do, the service guys are polite and know what they're doing.
Dale did a great job!
I needed help with a problem that I had my other AC guy out for 3 times. I called Air Force One because I use them at home to see if they would do commercial work. The did and they were able to have a technician out the same day!! Not only was Kevin quick and friendly, he found the problem and got me a quote to fix it...all on the same day.
System was overcharged. Recovered 1 1/2 pounds. It is working properly at this time.
Evaporator is leaking on the TXV capillaries. Will call gemaire tomorrow and see if they have evaporator in stock.
Put in leak sealant system is working to manufacturer specification
Breaker needs to be checked out by electrician. It is hot to the touch and smells Smokey. Customer signed up for 1 year membership.
Perform system maintenance found bad cap on downstairs as well recommended replacing as well as continual maintenance vet
Perform system maintenance found outside condenser capacitor going out expect as well as leaky ducks upstairs and high amps on upstairs system due to age Talk to the customer about recommended repairs customer declines at this time no further recommendations other than aforementioned
1 system spring PM. Checked blower motor amps and capacitor. Checked temperature differential. Inspected drain line. Replaced air filter. Checked condensing unit. Coils are clean. Checked fan and compressor amps. No issues found at this time. System is ready for summer weather.
Replaced control board for furnace. Tested system and it is blowing hot air now. No other issues found at this time. Customer signed up for presidential membership.
Need to return to replace circuit board. ICM282A. Also bring a 24X24X1 filter.
Quarterly Preventative Maintenance on 12 units
Up to 16 SEER 4 Ton Furnace with ECM Blower Motor
Diagnosed bad motherboard customer will reconvene with us on Monday to decide whether or not it is time for a new furnace or repair
High voltage wire going to carrier air handler was to small of wire for the amount of heating strips and burnt up. Cut back to bad wire and disconnected one heat strip tp allow system to operate safely.
Heating Check up 2 systems lennox furnace both systems are working great!!!
Replaced condenser fan motor and capacitor on rooftop carrier package unit