Have used their service for three years and it's always easy to do, the service guys are polite and know what they're doing.
Dale did a great job!
I needed help with a problem that I had my other AC guy out for 3 times. I called Air Force One because I use them at home to see if they would do commercial work. The did and they were able to have a technician out the same day!! Not only was Kevin quick and friendly, he found the problem and got me a quote to fix it...all on the same day.
Replaced control board for furnace. Tested system and it is blowing hot air now. No other issues found at this time. Customer signed up for presidential membership.
Need to return to replace circuit board. ICM282A. Also bring a 24X24X1 filter.
Quarterly Preventative Maintenance on 12 units
Up to 16 SEER 4 Ton Furnace with ECM Blower Motor
Diagnosed bad motherboard customer will reconvene with us on Monday to decide whether or not it is time for a new furnace or repair
High voltage wire going to carrier air handler was to small of wire for the amount of heating strips and burnt up. Cut back to bad wire and disconnected one heat strip tp allow system to operate safely.
Heating Check up 2 systems lennox furnace both systems are working great!!!
Replaced condenser fan motor and capacitor on rooftop carrier package unit
Replaced worn out contactor 1 pole and 5uf capacitor on upstairs condenser all working fine after fix..
TECHNICIAN RICK FOUND THAT THE SYSTEM HAS A FREON LEAK AT THE ON THE SUCTION LINE NEAR THE COMPRESSOR AND A CLOGGED THERMAL EXPANSION VALVE ON THE INSIDE COILS. SYSTEM USES THE OLD 410a FREON AND IT HAS ALL LEAKED OUT. REPAIR: - SYSTEM PUMP DOWN - REPAIR LEAK ON REFRIGERANT SUCTION LINE - ADD FILTER DRIER, AS NEEDED - CLEAN OUT INSIDE THERMAL EXPANSION VALVE - LEAK CHECK - CHARGE WITH 410aFREON - TEST SYSTEM
Tech found system had been turning off on high head pressure outside, system needed to be water washed. Indoor filter still clean. Drain line still clean. Just need to water wash condensing unit outside every 30-90days. Also recommend to add stones around unit to help keep clean.
Rooftop condensing unit needs start kit replaced. Customer will change out him self
DIAGNOSTIC ANALYSIS -1 RESIDENTIAL SYSTEM. Found outside dual run cap bad, replaced 25/10/440. Need to water wash condensing unot every 30 - 60 days. Cleaned indoor evap coil all stopped up. Also need to add ptrap for airhandler.
Installed tstat clear cover lock box on one of the lobby thermostats
Replaced half horsepower 240 volt 1075 rpm blower motor on rooftop gas package system unit number 19 Suite number 207 old blower motor running slow causing slugging to compressor and not pulling all the heat from the air