Although they did a excellent job of installing the two new units, I have one concern. Ten months ago I paid $425 to have two Jones valves installed in the drain lines. When the drain lines for the new units were installed the Jones valves were not included.
Great as always
Workmen were courteous and helpful, and answered my questions very satisfactorily.
1 system spring PM. Checked blower motor amps. Checked duct work and drain lines. Checked temperature differential. Replaced air filter. Checked condensing unit. Checked fan and compressor amps. Checked compressor capacitor. Coil is clean. No issues found at this time. System is ready for summer weather.
4 Ton 16 SEER Single Stage Lennox Merit System
Found outside downstairs unit low on refrigerant. Gave estimate for replacement. Performed system maintenance as far as possible.
Technician Ricardo perform preventive heat check on a Rheem airhandler all electric system replaced the special order filter owner had his own filters checked the evaporator and blower cleanliness passed just fine check off for heating elements and contactor points all for checked just fine each element pulling 20 amps which is normal and the temperature rise normal by manufacturer specs no other issues found system is ready for a cold winter we thank you for your business
2 systems rheem furnace heating inspection,filters were replaced carbon monoxide was checked levels normal no carbon monoxide inside of air stream systems are working properly.
Maintenance check up one system rheem furnace working properly.
Prepaid heating Check 2system rheem furnace both inspected all working great..
Blown out 5 amp fuse from the loose white wire @ tstat when finishing the closet.
Replaced under parts warranty evap coil & compressor 5ton 410a rheem system w/ filter dryers & 16 lbs 410a
Replace parts warranty only 5ton evap 410a coil downstairs equipment in the attic horizontally right. Also purchased 1yr club aggrement on 2 units.
Replaced evaporator coil for time air handlers system of the parts warranty recharge system all is working fine
Added 3lbs of r22 to syatem
Replaced trane control board, fan relay had burnt on old board
Blew out main and emergency drain lines, replaced warranty rheem 80mfd capacitor for the condenser. Main breaker for the a/c will need replacemwnt.
Replaced warranty contactor 1 pole checked refrigerant levels normal recommended service contract on both systems