Although they did a excellent job of installing the two new units, I have one concern. Ten months ago I paid $425 to have two Jones valves installed in the drain lines. When the drain lines for the new units were installed the Jones valves were not included.
Great as always
Workmen were courteous and helpful, and answered my questions very satisfactorily.
Summertime HVAC Repair for a residential homeowner near Merriman Park Elementary. Found a leak at the evaporator coil. Order replacement under warranty.
1600sq ft house. Went over options customer would like to review them and reach back out when she is ready.
Inspected unit for cooling cleared drain line andrinsed condenser. No other issues found.
Springtime Air Conditioning Repair for a residential customer near Woodbridge Parkway. Found downstairs system to be low filled with 7lb 12oz of 410a and UV dye pack. Scheduled follow up for leak check.
Replace 3 sections of duct that are damaged. Rehang and straighten any other disconnected runs. Ducts run correctly and decayed strapping redone.
Furnace Repair - Replacing flame sensors and flame igniters. Both are under warranty.
Cst mentioned slight gas smell by back door the other night but nothing found during maintenence inspection. All electrical and mechanical readings to standard. Outside unit found to be lightlyclogged with debris. After rinsing no other faults were found. Air filter replaced 20x25x4
Systems were both low on refrigerant. Added leak sealant and 410A to both systems. They are running good and operating normally at this time.
Raised float switch by an 1/8â€ because it was closing the downpour just enough to back the water up.
1 system spring PM. Checked blower motor amps. Checked duct work and drain lines. Checked temperature differential. Replaced air filter. Checked condensing unit. Checked fan and compressor amps. Checked compressor capacitor. Coil is clean. No issues found at this time. System is ready for summer weather.
4 Ton 16 SEER Single Stage Lennox Merit System
Found outside downstairs unit low on refrigerant. Gave estimate for replacement. Performed system maintenance as far as possible.
Technician Ricardo perform preventive heat check on a Rheem airhandler all electric system replaced the special order filter owner had his own filters checked the evaporator and blower cleanliness passed just fine check off for heating elements and contactor points all for checked just fine each element pulling 20 amps which is normal and the temperature rise normal by manufacturer specs no other issues found system is ready for a cold winter we thank you for your business
2 systems rheem furnace heating inspection,filters were replaced carbon monoxide was checked levels normal no carbon monoxide inside of air stream systems are working properly.
Maintenance check up one system rheem furnace working properly.