Great guys and very polite. Showed up on time and worked hard.
Airmax has been servicing my HVAC units for several years now. They are reliable and honest - they fix anything that is broken but don't upcharge or look to find false pretenses to incur additional work.
Mark Rose was tech
Mark always takes the time to explain things. Very considerate. G
On time, great job and reliable person through the years.
I used the company twice. Mark Rose is a good technician to work with. He did not only fix the problems but also explained the cause of the problems to me. This is the go to company for any AC issues I have in the future.
Mark always does a great job,, that’s why I always request him
I requested Airmax after AHS had assigned another company because Airmax's service is great.
Blake was awesome! He found and fixed the issue quickly. He took the time to explain it to me in a way I could understand and was extremely personable.
I appreciated Mark's helpful maintenance check of my HVAC system this winter. He even pointed out that the fan in my attic needs repair. I wouldn't have known to check for this myself.
Install new A/C Dallas
Did a 2 winter maintenance tuneup plus plan in Dallas TX. Checked blowers and capacitors, checked amps and ohmns, checked ignition, cleaned vacuum ports, cleaned flame sensors, checked limits and safety’s, everything is to manufacture specs. Discussed with customer about air scrubber.
Did a winter maintenance tuneup plus plan on 2 furnaces, carrier infinity systems, checked limits and safety’s, checked amps and ohmns, cleaned flame sensors, cleaned vacuum ports, checked variable blowers. Found everything to manufacture specs.
Did a 2 system winter maintenance tuneup plus plan renewal, both furnaces are 18 seer, communication systems. Checked limits and safety’s, checked amps and ohmns, cleaned vacuum ports, cleaned flame sensors, checked blower motor variable blowers, both units put in at spring of this year. Both meets manufacture specs.
Did a 2 system winter maintenance tuneup plus plan filters are provided by customer. Checked both units found downstairs furnace running too hot due to furnace being filthy along with evap coil. Suggesting duct cleaning, checked for leaking carbon monoxide found none. Checked limits and safety’s, checked amps and ohmns, checked capacitors all is good.
Preformed three system preventive maintenance.
Did winter tuneup
Found unit turned off in attic not allowing nest thermostat to work. Turned back on and tested thermostat to work properly. Suggesting maintenance.
Checked both unit furnaces for heating and found them both heating properly. Checked and cleaned flame sensors, vacuum ports,checked limits and safety’s, blowers and capacitors. Found them both to be with in mfg specs.
Did 2 winter maintenance tuneup plus plan prepaid. Checked ohms and amps, cleaned flame sensors, cleaned vacuum ports, checked all safety’s and limits. Everything is to mfg specs. Discussed with customer about cleaning duct work, and she watched video on the air scrubber. Leaving quote for both.
Insufficient cooling on an air conditioner in the North Dallas area