I've used AirMax for a long time. They give great service and work well with my home warranty.
Mark and Shelby did an excellent job for Heating Maintenance.
Always do a great job confident system is working as designed. Mark has a new helper who conducted the test in the system outstanding work!
Love Air Max. Anyone that has ever come for the install, bi yearly service, or special service calls have been extremely knowledgeable! The hay are very thorough in checking everything out, they are also very good exposing everything to you.
Very professional, quick and friendly service.
They were able to fit me in same day which was remarkable. Blake Childress was the technician. He did a thorough job and was super pleasant.
Happy with responsiveness and quality of service.
Their service is outstanding, I’ve been using them for years. Always consistent. Techs are polite and professional
The whole team has been fabulous, informative and they get the job done.
Blake did a great job.
Duct repairs Plano
A pond arrival found u/s not cooling found condenser wires all burnt up contactor not working, replaced wires and contactor. Then found fan motor not turning and replaced fan motor and 7.5 uf cap. Checked pressures and delta. Suggest maintenance yearly
Did a 2 system diamond winter maintenance tuneup in Plano TX. Checked blowers and capacitors, checked limits and safety’s, cleaned blowers, clean vacuum ports, cleaned flame sensors. Everything shows to be with in manufacture specs.
Did a 3 system winter maintenance tuneup plus plan in Plano TX. Checked blower motor and capacitors. Checked limits and safety’s, cleaned vacuum ports, cleaned flame sensors, checked furnace heating and “co” ppm 0 good, shared with customer about the air scrubber and left pamphlet with him.
Added new control board and system running properly found no other issues
Did a 1 winter maintenance tuneup plus plan, found new Lennox upflow furnace and found everything to be within manufacture specs. Checked limits and safety’s, checked amps and ohmns, cleaned flame sensor, cleaned vacuum port, checked variable blower and air flow. Checked heat rise of 47 ok. Talked about the air scrubber.
Did a 2 system winter maintenance tuneup plus plan one of the units are electrical and the other one is gas. There are 2 filters both were changed we checked limits and safety’s, amps and ohms on all motors, cleaned vacuum port, and cleaned flame sensor. The overall on both units meet the mfg specs. Both are heating properly.
Did a 1 system winter maintenance tuneup plus plan, changed filter, checked limits and safety’s, cleaned flame sensor, cleaned vacuum port, took delta.
Preformed two system heating preventive maintenance.
Water leaking issues resolved for a customer in Plano!