Replaced valve stems in hall bath
50 gal electric water heater tall needs to be replaced
Ultima 5600 head is leaking. Recommend replacing water softener. 32k grain. 24v.
Replaced Moen cartridge in hall bath tub.
Called out for a leak in the ground. Excavated down to pipe. Found leak to be from irrigation. Shut off irrigation supply. Customer will call an irrigation company for repairs.
Replaced 40 gal electric water heater
Replaced 3/4â€ ball valve on water service in laundry room.
Found leak in supply line to ice maker. Repaired and tested.
Estimate on new 3.5 ton split gas / and move condenser
Performed diagnostic found blower relay board bad recommend replacing. Blower VAD out of spec.heat Exaust motor running at max amps. Declines all repairs at this time.
Performed diagnostic found air leak and dirty coil. Cleaned evaporate coil and fixed air leak. Unit was cooling when I arrived. Blower V.A.D. Out of spec and heat exhaust motor at maximum amps could be issue when it is hotter.
Ac estimate for a new unit
Performed AC tuneup
AC tune up on Rheem system