Cleared hall bath toilet of soup bones.
Called out for water hammer sound. Tested PRV found it to be bad(90 psi). Replaced with new.
Found master bath shower p trap to be dry. Ran water to fill trap. Tested good no noises.
Replaced tank to bowl gaskets on master bathroom toilet .
Replaced tub spout in second floor hall bath. Installed customer supplied shower head and kitchen faucet.
Leaking water meter connection. Part is no longer made. Made spot repair on leak. Tested good. Recommend replacing water service from meter to house.
Installed customer supplied kitchen faucet
AIRE-FLO Air Conditioner Maintenance
Trane Package Unit Maintenance & American Standard Heat Pump Maintenance
Carrier Air Conditioner Maintenance
Repaired water leak in wall. Removed leaking 3/4” pipe and replaced with new. Tested good. ABS not responsible for wall repairs.
Lennox Heat Pump
York package unit maintenance
Trane Package Unit Maintenance