Replaced RO storage tank and filters
Inline recirculating pump needs to be replaced. 3/4” unions. Customer declined at this time.
Performed post audit. Units operating to spec. Fixed 2 duct run connections and tear in duct.
Replaced circulation motor under warranty. No cost today.
Performed diagnostic found bad circulation motor need to order from lennox and get back to customer. Tech. Kirk
Ac estimate for 2 split gas units
3.5 ton split heatpump