Rheem Air Conditioner Spring Maintenance
Ran kitchen drain from co to main. Cleared of unknown blockage.
Replaced 50 gal gas water heater. Plumbing inspection done at this time.
Replaced emergency shut off valve,fill valve and flapper in master bath toilet. Replaced tub spout in hall bath.
Cleared main line of unknown stoppage under house.
Performed diagnostic found unit low pressure lock out. Reset board pressures look good. Recommend changing filters every 2 weeks and switching to fiberglass filter.
Performed diagnostic quoted 1195 for air circulation motor found bad mounting bracket could not perform repair. Wants to get bracket welded and call us back to put motor in. If parts ordered from manufacture cost is $1793
Performed diagnostic cut 2nd stage on board. No charge today.
Performed diagnostic found bad comp. VAD and exaust motor VAD. Burnt and pitted voltage distributor replaced all and signed up on 4 year maintanence. 54 degree exit temp.
Diagnostic. Found 3 bad caps and burnt and pitted relay. Wires melted. Unit very old recommend replacing.