Fortunately my manufacturer's warranty covers parts and labor for all repairs, so I will not have to pay the $1200 plus to cover the repair. Parts are not likely to be available,
Arrived on time, job completed quickly and cleanley
Payment thru office
1 of 7 units not cooling
Need to order new motor Monday first thing
Rheem scheduled maintenance
Found the oldest unit low on refrigerant ( R-22 ) System is 16 yrs old & mis-matched ( Trane air handler, Nordyne condenser. ) Recommended replacement. Mohammed wants an estimate emailed to him on new system price. 3 ton split heat pump Lennox 14 seer.
Rheem and Trane scheduled maintenance
Tune up on 4 trane units
Rheem ac cooling service
Tuned up two Trane air conditioners
Performed diagnostic on Lennox unit.
Basement unit recently installed over winter. Found indoor unit frozen solid. Thawed out unit and removed large pieces of ice. Added roughly 2 lbs of 410a. Tightened shradder caps and king valves. Unit working fine. As a side note I noticed that there are 4 units next to each other outside. There is a Trane condenser that expells the exhaust directly into the other 3 units. When it comes on the high side goes up very quickly. If the units were to run a lot during a hot day this will cause issues with the other units. Recommend either replacing the condenser with a different model or trying to find a way to redirect the exhaust from that unit. All units cooling at this time.
Replaced indoor coil.