Rheem and Trane scheduled maintenance
Tune up on 4 trane units
Rheem ac cooling service
Tuned up two Trane air conditioners
Performed diagnostic on Lennox unit.
Basement unit recently installed over winter. Found indoor unit frozen solid. Thawed out unit and removed large pieces of ice. Added roughly 2 lbs of 410a. Tightened shradder caps and king valves. Unit working fine. As a side note I noticed that there are 4 units next to each other outside. There is a Trane condenser that expells the exhaust directly into the other 3 units. When it comes on the high side goes up very quickly. If the units were to run a lot during a hot day this will cause issues with the other units. Recommend either replacing the condenser with a different model or trying to find a way to redirect the exhaust from that unit. All units cooling at this time.
Replaced indoor coil.
Perform tuneup on rheem rooftop units for ACM member. All systems operating within manufacturers specs at this time
Tune up trane
Winter heating service heatpump
Winter heating service check 2 roof furnaces
I UNIT PMA CHECK, GROUND, GAS, NO SWAMP, **ADRIAN** customer has co monitor. No recommendations at this time. Unit is operational.