Representative was punctual, clean, polite, knowledgeable and professional.
Carrier air conditioner maintenance
Rheem scheduled maintenance
Carrier heat pump summer maintenance
Replaced heating elements on 80gal electric water heater. Hot water in cold side at faucets for the first few seconds may be caused by a bad mixing valve or hot water pipes to close to cold water pipes..
Preformed maintenance on two Rheem heat pump
2 unit pma check. Recently had indoor coil replaced on north unit. 45mfd phase shifter very low on tolerance and need to be replaced. South unit low on refrigerant by about 2 lbs. would not be a bad idea to have Alaskan come back by in about 30 days to check refrigerant level to be sure there is not a leak. Cleaned both outdoor heat transfer media. Replaced 45 mfd phase shifter. Both units cooling at this time.
Tune up on a carrier package unit
Extending a Preventative Maintenance Program for a long time customer and discussing Aeroseal duct seal.