Representative was punctual, clean, polite, knowledgeable and professional.
Preformed maintenance on two Rheem heat pump
2 unit pma check. Recently had indoor coil replaced on north unit. 45mfd phase shifter very low on tolerance and need to be replaced. South unit low on refrigerant by about 2 lbs. would not be a bad idea to have Alaskan come back by in about 30 days to check refrigerant level to be sure there is not a leak. Cleaned both outdoor heat transfer media. Replaced 45 mfd phase shifter. Both units cooling at this time.
Tune up on a carrier package unit
Extending a Preventative Maintenance Program for a long time customer and discussing Aeroseal duct seal.