David was kind, explained everything he was going to do and took care of the problem. Great Plumber professional.
Called to let me know when he would be here...a real plus for San Tan Valley!
Printed invoice and advertisement somewhat confusing. advertisement indicated 39.95 which included coil cleaning and no trip charge. Invoiced for all three at higher cost??????
Customer is gathering quotes.
Fresh tuneup on Lennox Heatpump
Replaced contactor on Carrier Alaskan Club Member winter tuneup
Completed a 40 point tune up for an Alaskan customer
Tune up carrier
Performed diagnostic. Put iso pads under compressor and unit. Loosened comp. screws.
Ac tune up on a Goodman split unit
Perform tuneup on trane unit for ACM member. All systems operating within manufacturers specs at this time
2.5 ton split heatpump estimate
System post inspection. Found small amount of oil on condenser pad below king valve. Could not find leak. Cleaned up with soap and water so if new oil comes back we will be able to find were issue is.
AC QUOTE FOR 3.5 TON SPLIT GAS 14 SEER
Doing a preseason maintenance tune up on a York air conditioner for a first time Alaskan Air Conditioning client