Tech came in did his job ,Efrain told us A/C unit was running good..
Getting ready to troubleshoot ac not cooling
Performing compressor replacement on carrier.
Performing diagnostics on carrier split system
Performing a no cool on the York 8 to 10-year-old split heat pump unit
Performing Tune up on York system
Doing a ac check on a splitheat pump carrier
David performed Alaskification and found evaporative coil severely rusted and drain pan full of water. Advsd need of replacement. Sanitized outdoor coil.
No heat on heat pump split system
Servicing ac system
Getting ready to perform maintenance on carrier ac system
Heating tune up carrier/service
Performing leak surch on ac unit
Air conditioning quote