Polite professional tech worked on our air conditioner. I will definitely use all seasons again.
Always a good experience , if we need help even on a holiday you are there to help
Logan Petro is very nice and personable. He says hello and uses my name. He does a great job and i feel comfortable with him in our home. We are very pleased eith his work and your company's service. Thanks again! 😃
Logan is the “Dude”
Very good service
Excellent overall service
Yancy Stover, a Lennox technician was sent to our condo to setup and and pair our phones with our new AC/Heat pump system that we had installed the last week of Dec. 2021. Yancy did an excellent job of setting up, pairing our phones, and explaining how to use them and how the system works. He is in our opinion is a pleasant, polite and very patient person that really understands how the Lennox system works and is able to trouble shoot quickly when the tech info in the system doesn't want to cooperate. Being a Industrial Technology teacher for the past 40 years, I just want the company to know that you, in my opinion, you are fortunate to have a very valuable employee like Yancy Stover. It's employees like him that give your company a good reputation and name. We are very happy you sent him. Brian and Maggie Boucher Port Holiday Dr. Building 9 Kimberling City MO
It is always a through service
That’s why we got unit from all seasons and would again
Logan was very attentive and answered all of my concerns. He was very thorough with our annual heating inspection.
Came to see why upstairs bedroom was hotter than the rest of house found that bedroom was under fed with supply air
Planned maintenance agreement cooling tune up on a Lennox duel fuel system. Checked it out and found it to be operating properly.
Came out to find out why an Arco air heatpump wasn't cooling. Found that the run capacitor had went bad. Replaced it then I found that the systems was low on charge. Added 4 lbs r410a. To get it cooling then found the leak in the indoor coil
Came out To clean an evap coil and to pull and clean a blower wheel on a 90 model Lennox heatpump. Got everything done and checked to make sure that the system ran.
Doing a tune up on a carrier a/c that was not cooling due to a failed capacitor.
Complaint of no a.c and wants system maintenance started. Diagnosis- Found system with a bad heat sequencer causing heat to tamper the a.c and thus no cooling. Solution- unhooked heat sequencer for meantime until we can replace sequencer in fall. System now cooling properly.
Giving a bid for replacement on a rheem heat pump system
Doing a tune up on a Lennox heat pump system.
Working on a Lennox heat pump that is leaking water due to a plugged drain. Also doing an ac tune up to ensure proper operation.
Planned maintenance checkout on trane high efficiency heat pump. System looks great at this time.
Planned maintenance checkout on lennox heat pump system. System looks great at this time. See tune up sheet for more Information regarding this service.
Working on an Amana heat pump that is tripping the 30 amp breaker, due to a shorted wire in the disconnect box outside.
Replacing an outdoor fan motor on a Lennox heat pump system and completing an ac tune up.
Came out for ac tune up on an American standard heatpump. Found that the systems was under preforming due to being low on refrigerant. Added 410a to get the system operating properly. Found that a contactor was trying to fail so replaced to keep from having a breakdown.
Planned maintenance agreement cooling tune up on a Lennox variable speed heatpump. Check the system out and found it to be operating properly.