Very nice and cleaned up well
We’re able come come the day I called and fixed the problem quickly!
I was kept informed every step of the repair process.
Logon was awesome and got us fixed within a matter of minutes!
Zack ran into issues that were unexpected, worked through them and over all, provided excellent service.
Zach was great and took care of our issue in avery timely fashion. He also was great explaining the problem and how he repaired it.
All Seasons is the best! Belinda got us set up for service ASAP. Logan, our awesome technician,was here right away and took care of our problem! He serviced our AC as well! Really appreciate this company!! Highly recommend 😀
Installers did a great job. They advised us as to what they were doing. They were respectful of furniture and floor coverings they had to work around. They cleaned up after their warm was done. They were very professional and still fun to have around.
Complaint of a.c not keeping up, set at 74 and 80 in the home
Bid on system replacement. Gave customer options on goodman dual fuel and lennox dual fuel. Customer will let us know on what he decides to do going forward.
Complaint of outdoor fan motor not working. Diagnosis- Found shorted fan capicitor. Solution- Replaced fan capicitor and did system cleaning. System looks good at this time. System is older and will need annual maintenance to insure the most longevity possible.
Arrived to find system operating properly. Found an airflow issue. Doors need to be replaced to Louver doors or needs to cut in return air grills in the walls to help move air. Across the rooms. Left doors open. Unit dropped seven degrees before we left. Unit is cooling at this time.
Came out for planned maintenance agreement cooling tune up on a climate master geothermal heatpump. Found minor problem with the filter being dirty. But rest of system was working properly.
Installing a new Lennox heat pump system. Replacing old system that was hit from machinery, and needing replaced. Replacing lineset. Brazing in new equipment. Pressure testing system. Evacuating system of all moisture and oxygen. Charging system to manufacturer recommendations. Re-doing a dryer vent run. And removing old equipment from the property.
Installing a new Lennox heat pump system. Replacing an old R22 system that was leaking and no longer cost effective to service. Removing r22 refrigerant. Cutting loose old equipment. Setting new equipment. Brazing in new system. Pressure testing system. Evacuating system of oxygen and moisture. Charging system to manufacturer specification. Testing equipment operation and thermostat operations.
Installing a Lennox variable capacity communicating system. Removing old equipment. Flushing out lineset to remove contamination. Brazing in new system. Pressure testing system. Evacuating system off oxygen and moisture. Charging up system to manufacturer specifications. Setting up smart thermostat. And testing system operation and performance.
Lennox heat pump cleaning and condenser fan motor replacement
Complaint of no a.c, compressor will run but not outdoor fan motor. Diagnosis- Found shorted dual run capicitor and condenser fan motor bearings out most likley due to wear and tear and partially from weak to shorted run capicitor. Solution- Replacing condenser fan motor with new oem part and replacing defective capicitor.
Working on carrier heat pump with intermittent low voltage short on a call for air conditioning. Diagnosis- Found sun rotted thermostat wire bleeding 24volts to unused wires causing a internal short in outdoor electrical compartment. Solutions- Isolated wires from one another and completely reinsulated wire bundle. Cycled system multiple times and is showing normal operation at this time.
Rheem air conditioner not keeping up. Found system low on r22, Informed customer of where I found leak and what options he had. He wanted to add charge today and keep on maintenance until replacement is needed.
Complaint of poor airflow, not cooling. Diagnosis- Found A coil plugged with dirt and debris. Customer needs to get plumber to address sewage backup into crawl space to be able to see ductworks condition.
Planned maintenance checkout on goodman heat pump system. System looks great at this time.
Replacing a compressor under warranty on a Lennox AC system. Brazed in new compressor. Pressure tested system. Vacuumed system under 500 microns. Recharged system to factory requirements. System operating properly at this time.