Logan was thorough and professional We couldn’t have been more satisfied
Honest prompt help. Thank you.
Replaced specialized zone damper and tested system operation. System looks great at this time.
Planned maintenance checkout on two mitibushi mini splits and 1 York split system heat pump. All systems look great at this time.
Planned maintenance checkout
A.c not cooling, Goodman heat pump system. Diagnosis- Found system low on r22 freon, added 2 pounds of new r22, checked system operation and also found bad-weak capacitor 35/5, replaced with new 35 and 5 and rechecked system operation. System showing normal operation at this time.
Replacement of indoor evaporator coil on Rheem heat pump system. System is now showing normal operation at this time. Would recommend annual service
Installation of new lennox signature series heat pump system.
Planned maintenance checkout on lennox heat pump system. System checked out great at this time.
A.c checkout on two zoned carrier systems. Both systems showing normal operation at this time, went ahead and got units cleaned out and filters changed. Also went over customer education as theses systems are new to them.
2 heat pump systems checkouts in a.c mode. Both systems check out great at this time.
Trane heat pump dual fuel communications problem.
Working on a.c unit not cooling. Found bad compressor shorted to ground. Customer decided to replace system with new lennox heat pump.
Gas furnace not heating
Customer education on thermostat operation with new Lennox heat pump installation.