Tech arrived prior to scheduled time which was great! He completed the PMA and explained what he did and was quick.
Was here on time and worked hard to complete job
Was here when they said they would be
I was very pleased with the installation of our new geo thermal unit. Courteous and competent installation crews. Great office personnel. A pleasure to work with.
Response from All Seasons Comfort Systems LLC:
We appreciate the great review! We are fortunate to have skilled personnel that have a vast knowledge of geo thermal heat pumps and are pleased to have been able to provide the best system at the best price for you. Thank you for your continued business and we look forward to working with you for years to come.
Efficient, knowledgeable and maticulous.
No a.c on carrier heat pump with Gibson outdoor unit. Diagnosis- Found outdoor unit fan run capicitor shorted. Solutions- Replaced run capicitor and tested system. Looks great at this time.
Bid on system replacement of rheem gas and a.c
Working on a cs7500 thermostat that is not reading the proper temperature
Performed a full geo inspection. Checked all wires and safety switches. Checked water pressure. Unit is cooling properly at this time.
Came out to find out why thermostat wasn't working. Found that thermostat was bad replaced thermostat with honeywell pro 5000 thermostat. To get the system operating properly.
Repairing exposed leak in attic.
Complaint of no a.c error code 180 on new trane- American standard dual fuel system.
Planned maintenance checkout on Rheem Heat Pump system. System looks great at this time.
Complaint of a.c not blowing cold air. Diagnosis- Found system low on charge, customer did not wish to find leak just add for the meantime. Added 2 pounds of r22 and tested system. System now operating properly at this time.
Lennox thermostat costumer education on operations
Replacing a compressor under warranty on a Lennox heat pump system. Removing refrigerant charge. Brazing in new compressor. Pressure testing system. Performing a system evacuation. Recharging system refrigerant. And testing system performance after repair.
Geo thermal tune up no issues found
Planned maintenance agreement heating tune up on lennox heatpump. Found system to be operating properly.
Heating tune up on lennox gas furnace. Found that the system was operating properly
Planned maintenance agreement heating tune up on colman gas furnace. Check the system and it was operating properly