Aubrey, the All Seasons service tech was professional, friendly, and knowledgeable. He efficiently repaired our a/c, had the need parts with him and thoughtfully answered all of our questions even after performing the repairs in the searing 100 degree heat. All Seasons service price was reasonable and we were appreciative of their prompt response.
He is knowledgeable and will trained.
They did great work in a timely fashion
Prompt service, very courteous
Logan Stover was very professional, polite, and diligent.
Aubrey resolved my problem with the filter sizing and I am very pleased with the new filter.
Logan really explained everything he was doing. I need to stay with him because of the cats so it helped to see there was breakers in the furnace. And how he tightened screws due to vibration and how he cleaned coils to keep the system clean. So much in ffg ormation thank you Logan.
We were out of town when our 15 year old furnace developed a coil leak. Logan called us & discussed various options with us. We decided to go with a new furnace. All Seasons personnel got us the new furnace, coordinated with our neighbor’s schedule & was able to install the new furnace during the same week (earlier than they quoted). The price was great!! Service excellent. On both visits, Logan called & kept us posted on his progress.
A.c not cooling on mobile home system.
Performed a full cooling inspection on Goodman equipment. Checked all wires and safety switches. Found some duck work hanging low to the ground. Tightened up duck work. Checked for air leakage. Found a leak in another part of the ductwork. Repaired all duck work. Performed safety testing to ensure no leaks at this time. Unit is now operating properly at this time.
Faking mini split leaking water found line set not covered and lines condensating pulled insulation tight to cover line
Complaint of goodman/carrier a.c not cooling. Diagnosis- Found low subcooling and high superheat, low delta T. Solution- Added 1lb of R-22. System cooling properly at this time.
Bid on total system replacement on old York a.c and gas furnace.
Complaint of no a.c, indoor unit running outdoor unit off. Diagnosis- Found shorted Dual Run Capicitor. Solution- Replaced Capicitor with new, checked system charge and amp draw of motors. System looks great at this time.
Servicing a Rheem heat pump system with a leaking condensate drain line and performing a system tune up. Cleared condensate drain blockage. Tested drain. Cleaned coils. Checked system charge. Replaced air filter. And checked overall system performance.
Working on a Ruud heat pump that is leaking water. We found that the drain pan was full of rust and plugged the drain.
Came out to do a cooling tune up on a geocomfort geothermal heatpump. Found that one of the four zone dampers were bad. And found that the system was under preforming in cooling mode. Was able to dial the system in by adding water. Got the system operating properly.
Came out to install a low pressure switch on a lennox heatpump. Found that the switch was not working after changing Reversing Valve. Got the switch installed and made sure the system was operating properly.
Came out for reeheem system not cooling found start Capacitor and run Capacitor bad replaced them to get system operating properly
Came out to do a check on a napoleon heatpump. Made some minor adjustments to fan settings and checked the charge. System was operating properly.
Came out for lennox air handler making noise. Found that there was insulation in the blower causing it to be out of balance. Removed insulation and repaired cabinet to keep it in place.
Installing A blower control board in a Gibson heat pump
Working on a Mitsubishi mini split that is not cooling properly.