Tech Logan was wonderful and very knowledgeable of our system and went over everything with us. No else will replace him in our house
Logan always locates any problem in a quick and timely manner.
Logan arrived at set appointment time. Detected problem Immediately. Replaced parts needed and all is good. Highly recommended.
Fast service with scheduling, excellent office ladies. Service was fast and problem was fixed correctly first off. Not a problem since. Recommend to everyone looking for great trustworthy service!
Response from All Seasons Comfort Systems LLC:
James thank you so very much for the great review! We appreciate you taking the time to provide a 5 star rating for Logan and the office staff. We're committed to providing the best possible service and get our customers up and running as quickly as possible. Thank you for your business and we look forward to serving all of your home comfort needs!
Bid on adding humidifier to main system.
Working on a Goodman heat pump that is not heating due to a failed blower capacitor.
Planned maintenance heating checkout on air ease heat pump and checked mini split operation. Both systems working properly at this time
Planned maintenance heating maintenance on 2 lennox dual fuel systems and 1 heat pump system. Got all 3 systems tuned up, filters and humidifier pads changed and checkouts completed. Systems look great at this time
Lennox wifi thermostat intermittently loosing connection and operation. Set wifi back up, updated thermostat and ran system through multiple cycles while doing maintenance. System showing normal operation at this time.
Planned maintenance checkout on two nordyne heat pump systems. Both systems look great at this time.
Two maintenance checkouts on Goodman heat pump systems. Got both systems cleaned throughly and both systems checked out and inspected great at this time.
AC Repair - Planned maintenance checkout on carrier a.c, filter change and cleaning.
A.c checkout on Bryant heat pump system. System showing normal operation at this time. See tune up sheet for more information regarding this service.
Complaint of heat pump air handler staying on constantly. Diagnosis- Found 1 stuck heat strip sequence and another stuck control board relay. Replaced sequencer and got control board on order from York.
Installed two new Lennox Heat Pump systems. Tested both systems in heat and cool. Both look great at this time.
Installed new ptac heating and cooling system. Tested and setup system and went over customer education. System working great.
Complaint of outdoor unit not running in heat pump mode. Diagnosis- Found thermostat accidently set to emergency heat. Went ahead and did systems check to insure system running properly. Everything looks great at this time.
Complaint of no indoor fan operation. Solution- Found loose spade terminal connection on blower relay. Replaced spade and tested system. Running properly at this time.
Planned maintenance checkout on lennox heat pump system. System looks great at this time.