PMA Heating tune-up 2- units Gas furnaces w/A/C. Both systems check out great at this time. See tune up sheet for more information regarding this service.
Goodman a.c not cooling. Diagnosis- Found outdoor unit thermostat wire shorted. Solution- Cut out bad piece of wire and ran new 2 wire to unit. Tested system afterwards and everything looks great at this time.
Complaint of upstairs unit not cooling, blowing warm air. Diagnosis- Found shorted factory warrantied capicitor. Solution- Replaced with new 40-5mfd capicitor and checked charge and temperature split. System working great at this time.
Doing a tune up on a Goodman heat pump system
Bid on system humidifier installation.
Planned maintenance checkout on two heat pump systems. Both systems checked out great.
Pma heating checkout on two Bryant Gas furnace systems. Both systems look great at this time.
Service call on noisy indoor unit. Diagnosis- Found system to have high static pressure in duct work and have multiple areas where metal is touching metal causing high noise on startup. Solutions, put rubber isolation pads where I could to reduce noise.
Replacing thermostat on HVAC system
Heating system not operating properly
Condensing unit coil changeout in lampe mo
Install ground-source geothermal system
Rheem heat pump making loud noise on startup in highlandville mo
System checks on 3 heat pump systems