I am glad we did it
The two Logans were together and worked as a team to solve my HVAC issus. Both were very knowledgeable and answered the questions I had, demonstrating great professionalism.
He came earlier than I expected. That was good, I had no heat. He new exactly where to look and fixed the unit quickly.
Planned maintenance checkout on lennox heat pump
Complaint of downstairs thermostat glitching.
Planned maintenance checkout lennox heat pump system. System looks great at this time.
AC Repair / Heat Pump Repair - Working on a carrier heat pump that is not working due to being low on charge.
Working on an I harmony zone control that is not allowing the downstairs thermostat to work
Annual maintenance on heat pump package unit
Installed new high efficiency gas furnace. Tested furnace after installation for correct gas pressure and operation. System running great at this time.
Complaint of trane package unit heat pump system with blank thermostat. Diagnosis- Found low voltage short on wiring harness going to pressure switches. Solutions- Replaced 3amp fuse and reinsulated wires. Tested system and showing normal operation at this time.
Complaint of poor heating, not keeping up. Diagnosis- Found heat pump system heating as it should with cold temperatures. Went ahead and did full systems checkout. Unit looks great at this time. Informed customer it would run pretty consistently with current weather conditions. Also went over defrost operation with them.
Setting up the WiFi on a nee Lennox xp20 zoned heat pump
Heat pump system changing out heat pack due to corrosion and wear.
Installing and setting up an I-harmony zone panel on a Lennox heat pump system after new installation
Annual maintaince on lennox heat pump systems in walnut shade mo.
Tune-up on heating HVAC system
Service call on mini split not cooling