Have any feedback for us? We'd love to hear it! Call us at (703) 997-8655 and let us know how we are doing.
I’ve used Arctic Suns service three times in the last two years. From scheduling to the the service technician coming out I’ve had nothing but great service.
We had a plumbing inspection Preformed by Jeremy and William and it was found that we needed a pressure release valve to be installed because our water pressure was extremely high. Jeremey and William were a great team. They explained everything to me and took care of our problem seamlessly. All materials were on the truck so I didn’t have to reschedule another appointment.
Tim is a superb technician, efficient, kind, considerate, and a good listener. He goes beyond the call of duty to provide excellent and preventive service. It’s always a pleasure to visit with him.
Excellent communication. A very nice experience because representative explained all he did.
Great! Very friendly and considerate.
We are extremely pleased with the service we have had from Arctic Sun Heating and Air Conditioning. We have been customers for a few years now, thanks to the professionalism, friendliness, knowledge and effort shown us by the employees. Sam D.’s main goal is to make sure our furnace and air conditioner are working in top shape and providing the most comfortable air temperature throughout our home, all through the year. My husband and I highly recommend this company with 5 stars.
Tim was very professional and knowledgeable.
Service on gas furnace check all working good on heat.
Installed nest thermostat and check all working good on heat
Service on goodman gas furnace and thermostat check capacitor check blower motor inducer motor check heat exchanger check all safety switches check filters and clean drain line all working good on heat
Checked motors, capacitor, filter, vacuum switches and tubing, wiring, blower, thermostat, flue, limit, cleaned burners and flame sensor. Everything working properly
Checked motors, capacitor, filter, wiring, blower, limits, vacuum switches and tubing, pressures, cleaned burners and flame sensor. Everything working properly
Install new condenser motor on Carrier heat pump.
Service on gas furnace clean furnace and flame sensor check heat exchanger check blower motor and thermostat check all safety switches clean drain for furnace,all safety switches working good on heat.
Heat not working after diagnose found blower motor and cap also ignited reading low,replace all and test working good.
Maintenance on oil boiler
Checked dual fuel system. Checked motors, capacitor, filter, thermostat, wiring, drain, blower, refrigerant, coils, vacuum switches and tubing, defrost, limits, cleaned burners and flame sensor. Everything working properly
Checked motors, wiring, capacitor, pressures, limits, vacuum switches and tubing, filter, thermostat, cleaned burners and flame sensor. Everything working properly
Checked filters, blower, motors, capacitors, vacuum switch and tubing, thermostat, wiring, cleaned burners and flame sensor. Wipe unit with protectant. Everything working properly
Service on Amana heat pump,check blower motor and compressor check capacitor check filter check freon,all electrical wires,freon all working good on heat.
Checked motors, capacitors, blowers, vacuum and tubing, gas valves, pressures, filters, blowers. Cleaned burners and flame sensor. Flame sensors need replacing. Customer does not want to repair at this time. Everything working at this time
Replaced burner in the gas furnace and text all working good on heat.