He replaced the bad part and our home started cooling right away. Next day it was making a noise and they set appt to be here within hours but the noise stopped so we called to tell them. Hopefully it will do fine but they assured us if any problem just call. Thank you for your service
Performed (1) system heating maintenance. Found some potential concerns on the heat exchanger.
Called in with a condenser fan not working. Arrived to find out the fan was the issue and replaced the fan and got them back up and running.
Unit not cooling went to do diagnostic.
added 3lbs refrigerant to heat pump
Cleaning a condensing unit