As always, fast, friendly, and professional
Outstanding job got the job done in a timely matter thank you
I have used them twice, have received same day service. Tech’s are friendly and get right to the problem.
The company representative showed up quickly and explained what was going on with the heater/air conditioner. Within half an hour he had everything fixed and running smoothly once again. He also gave me instructions on how to keep the system in good working order.
Don was excellent
As always. Very satisfied
Top notch, professional and happy we chose them!
Acquire information to quote ducted mini split for garage conversion. Will have price by Monday for Homeowner
Low voltage fuse blown bad contactor for heating elements, replaced check out other low voltage replace fuse, check operation in Heating functions normal. Quoted system replacement due to age.
Found indoor blower not operating. Determined that blower module is bad. Outdoor unit will run. Instructed homeowner to leave unit off for now and quoted to install and Evergreen blower replacement module. Unit is not under any warranty
Low voltage fuse blown, straight Cool heating system discovered shorted contactor, replaced and check unit. 41 amps Heat operates normal
System blower motor not running. Ordered blower motor and indoor board may not need both. Will call with repair quote. Bill customer
Repaired burnt terminals on heat strip wires. Bill customer
customer given estimate on new tstat. Called for o circuit in heating causing air to run in heating cycle. Customer will call. Disconnected o circuit in outside unit.
Low voltage short vlown low voltage fuse checked heat kit it was good checked reversing valve its good found white wire to condenser bad causing short changed white to brown in air handler and condenser installed new low voltage fuse cycled tested unit running at this time 1st yr warranty
Found low voltage reading 17 traced problem to control board replaced board found bad cap replaced unit working properly at this time
Low voltage for heat strips was not connected. Ran heat at 34 amps. Advised customer he does not have heat pump electric heat only.
Checked operation of unit, found unit pumping down in heating mode. Cap tube on sensor bulb for heating txv has rubbed through and lost its charge. Txv will have to be replaced.
Installed customer supplied thermostat due to old thermostat not heat pump compatible. Tested both heating and cooling functions all ok. System operating in cooling and heating modes at this time.
Explain operation of thermostat to homeowner homeowners phone would not support ecobee app
quoted new system
Replace bad thermostat, corrected wiring to thermostat ,check system system running normally at present time