Mr Diaz is an excellent, professional, courteous and knowledgeable answering all my questions. My experience with Mr Diaz was outstanding. Also very thoroughly completed and solved the issue with my AC unit. Thank you will highly recommend.
Tyler was efficient and personable
True Young gentleman
Rob has been out to my house several times and he always does a great job.
Tyler came and fixed the problem in minutes. Explained what happened quick and professional.
Guys came was easy quick no problems at all! Courteous and polite!
I think Andrew was very informative he explained all my options clearly. Very nice young man polite and knowledgeable. He was waiting for me to get home from work, which was really great!
Great experience Andrew was excellent explaining all my options and detailed explanation of the repairs needed.
He was here went right to work knew what he was doing answer all questions was friendly and kind . I was very impressed with his work .
Everything was handled very professionaly
Bay Area is my first call for all AC work, big or small with 2 commercial businesses and 4 houses. Attention to detail, quick service, reasonable prices, QUALITY work.
Replace bad contactor and dual run cap also repaired wire end and suggest replacement left estimate on new equipment,
Cleaned indoor and outdoor coils as well as drain line and treated drain pan with antimicrobial agent. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Unit is running and draining fine.
Found indoor unit TXV stuck shut. Causing unit to pump down and Cooling and freeze coil. Which caused code 83 low pressure shut off and made the unit lock out till 3 hours later which did thaw the coil and unit ran again. Turning unit on into heating all pressures and temperatures look normal. Ordered new part. Office will call to schedule.
Thermostat not sending any signals to equipment. Bypassed thermostat and system began cooling. Spoke with customer about changing out and they agreed. Changed thermostat and unit is running fine.
Service call completed, upon arrival condenser unit copper pipe make contact with fan motor line wires and broke copper pipe and leaks all the refrigerant, repair pipe and replaced refrigerant from r-22 to MO99, after repairs check system operations, unit is cooling at this time, advised client systems age and condition, provided with options and recommendation, client agreed only with repair at this time
Changed out thermostat for blue easy reader thermostat so customer can see it better. Ran and tested system and registered product. Thermostat had a two year labor warranty and a five year part warranty.
Retrieved information for two commercial unit contracts
Cleaned indoor and outdoor coils as well as drain line and treated drain pan with antimicrobial agent. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Found system with extraordinarily high static pressure on the supply side. Went and looked at duct work and found supply plenum quite restrictive, and that the supply duct itself is only 14". Based on the tonnage of the unit it would require a 16" supply duct. Spoke with customer about duct problem and she decided to go with our recommendation. Put in work order for us to come back.
Installed ONE Temporary portable unit until 3/9/22 when new system is put in. Could not find a good location in bedroom for the 2nd one due to conditions.
Performed preventative maintenance and cleaning. Checked all electrical connections and components. Checked refrigeration operations and pressures. Checked heat controls and operations. Cleaned indoor and outdoor coils. Cleared condensate drain and treated pan. Found no issues during this visit. System is in good operating condition at this time.
Install new duct cover. Need to return with concrete patch and caulk.
Installed 10 kw heat strips, ran appropriately sized wire from new disconnect in attic, and installed new disconnect outside. Tested unit which is now getting a 20 degree temperature split as opposed to the original 12 degree temperature split. Unit is running fine.
Maintenance completed, drain and flush condensation line, advised client to replaced air filter regularly, clean evaporator and condenser coil, during maintenance noticed evaporator coil moderate impacted with rust, system is operating at this time, due the age of the system I send a complementary system replacement quote on the email on file
Maintenance completed on mini split system located on the master bedroom, check system operations, all systems vitals are good at this time
Maintenance completed on mini split system located onto guest room , all systems vitals are good at this time system