Don was very thorough & courtious.
Would highly recommend him
Don did a great job repair our AC and explained everything in detail.
Tech was on time. He diagnosed the problem and fixed it right away.
Service person knowledgeable and efficient
Called late last Friday as a/c was not cooling. Robert came out within an 1-1/2 hrs. Got the a/c running quickly (in the dark). Explained the problems that he was seeing in our 15 year old unit and offered some long term solutions. Very professional and courteous.
I contacted Bay A/C INC based on their “Best A/C service in Citrus County”. They deserve that rating!
I was a really good experience person , respectful, honest who new was he’s doing patiently explained everything was he was doing and anything I asked. Would definitely do bussiness again and ask for Keith Reasonable prices
Customer called due to system not operating customer tried replacing capacitor themselves compressor is no longer operating. Customer requested quote for replacement of system and or compressor replacement. Checked over system to verify units compressor has failed. System not operating at this time leaving quote for compressor replacement and system replacement.
Replace outdoor fan motor capacitor was replaced earlier this week. .5 FLA .3 ALA
Still insufficient cool check charge, power washed evaporator coil again. Add a 3 lb refrigerant. System has 5/16 liquid line low head pressure high suction
System was Todd when I arrived unit was icing up due to completely impacted filter home inside is undergoing extensive remodeling instructed homeowner on proper use of filter during construction and options or when construction is finished. Ask homeowner to call once construction is done to schedule an early morning call and I will climb through the attic and check their ductwork
qte reme 7 units
Check up on a carrier heat pump pkg unit
Blown capacitor replaced and checked. Will estimate fan motor and quoted new equipment
Scharder core leaking through cap nut , unable to Tighten or remove Schrader core put on new schrader cap tightened not leaking at present time
Check up complete
Sound evaporator coil completely iced up. Unit is a straight cool was unable to thaw. Inform customer someone would be back tomorrow to check
Tom suction pressure of system low added. Added 1 lb R22 to bring suction pressure up past freezing was able to examine evaporator coil evaporator coil is very dirty needs to be cleaned estimated quote will be sent to pull and clean coil
Check up on a carrier 3ton heat pump
Manager Barb canceled call when I arrive she said she found out a homeless person had turned off the disconnect
Check system unit is working properly at this time
FOUND SYSTEM OFF ON FLOAT SWITCH. FLUSHED DRAIN LINE AND PAN. SYSTEM IS OPERATING NORMALLY AT THIS TIME