Very happy with the service price! Always scared when I need to have service on my central air like I dread having to talk to an attorney! They drain the pocket real fast!! They’re the cheapest around that I’ve found so far and didn’t pressure me to buy a new unit!! Glad that I had them out and they came fast, within hours of calling them at no extra charge!!
Fast, professional, personable service.
Service technician was very knowledgeable and thorough. Price was very fair for Service call and work that was done
I was so very glad they were quick to respond to my needs. The work was done quickly and efficient. Jamie was very kind and helpful. Thank you!
Diagnosed and repaired quickly and professionally.
Found and adjusted the low refrigerant level, found a leak on the condenser coil, need to replace.
Found and replaced the failed float switch, checked operations.
Flushed out drain line, checked operation
Ordered drain pan & insulation
Replaced run capacitor for blower motor with 20 uf need to come back with 15 uf cap
Performed preventive maintenance. System is operating properly at this time.
Found heat pump running normally, but electric heat strip had wire corroded off of terminal which will not allow electric heat to come on during defrost. Have to replace heater due to unrepairable male terminal on heater. Ordered heater and will return and replace.
system operating and functioing
system operating and functioing properly
Replaced defrost board, checked both heat & cool to come on 917178A board #
DF board has short in it would come on sometimes & then not come on, ordered board
Went into attic and listed all flex runs and lengths to replace existing flex runs. Also 3 supply air registers in ceiling. Will get back to customer with price to complete job.
Performed the annual check up, found and replaced the failed t-stat. All modes work promptly at this time.
Performed the annual check up, found and repaired the loose condenser fan wire connector, all modes work promptly at this time.
filled out job info for install