Installed and tested new Infiniti Thermostat. System is working properly.
10 YEAR PARTS AND LABOR
Found drain plugged and condensate pump Cleared drain and pump. Flushed and treated
Gave customer a few prices on unit found that i.d blower motor is bad did Pasco parts order
Found no problems at this time with system or t-stat. Customer is getting used to stat and finding where to set stat for when not home nd when. This is a get away home and temperature and humidity are back an forth do to that. Se is going o etc her away settings now so that the humidity and temperature are to her satisfaction. She is going to log settings and then find the sweet spot for there comfort needs. That being temperature and humidity. Explained as well as i could that stat if cooling will only allow 3Â° below to satisfy humidity. If that is to cold then will have to raise temperatures and humidity then will go up as well
10 year parts and 1 year labor warranty
Installed new thermostat and tested. System working properly.
Replaced contactor that was stuck in closed position. Restarted and tested cooling. Customer wants 12x12 return grill cut in secondary bedroom. Cost will be $150 Customer approved.
Service call completed, primary safety switch open on arrival, drain and flush condensation line and advised client to replace air filter regularly, all system vital are good at this