Service Tech represented your company extremely well.
I recommend this company
I will recommend the company to everyone.
I will call again when you are needed. thank you ! Carl
I have nothing but good things to say about this company. I have used them several times over the past number of years and they have always been exceptionally responsive and reasonably priced. This was put to the test this past weekend. Our air conditioning went out at a house we had guests at about 8:00 pm on a Saturday night. We called their emergency number and they had someone at our house in about 30 mins on a Saturday night. Unable to fix it that night because they needed a new pump, they were back early the following Sunday morning to complete the repairs. Because of them our guests’ weekend was saved from being ruined. This company has great customer service and highly qualified technicians. Highly recommend them. They are the ONLY air conditioning company we use in the Crystal River area and they have certainly earned our loyalty.
Indoor blower motor bad left estimate on replacing blower motor and also left estimate on new equipment suggests new equipment over repair due to age and condition awaiting decision
replace bad cap
Was giving module when needed whole motor " running backwards" replace motor system running normally at this time
System module bad change speed tap from one to speed tap 2 to have run for time being, module was installed in December of 2019 will have Parts double check for warranty
found bad x13 motor unit out of warranty new homeowner ordered blower motor
drain clog, no flush t e e. Installed flush tea and blew out drain. Repair loose line voltage at contactor outdoor unit. Instruct customer on float switch and filter. Drain flows normal system operates normal.
Leak search system could not find leak.
Added 3lbs r410a to system. Conducted leak search found leak at txv flare fitting . Tightened flare verify with soap. Reschedule to return in 2 weeks to be sure there is no other leaks.
Customer called due to systems A/H not shutting off checked system operations in cooling all ok. Found systems thermostat programmed to keep fan on. Changed fan settings systems fan is shutting off normally system operating and draining correctly at this time. Spoke to customer he is going to call office and pay bill.
MECHANICALLY CLEANED INDOOR AND OUTDOOR UNIT. FLUSHED DRAIN LINE AND PAN. ADDED DRAIN TREATMENT. VERIFIED ALL AMP DRAWS AND ELECTRICAL CONNECTIONS. CHECKED ALL REFRIDGERANT LEVELS AND TEMPERATURES. SYSTEM IS OPERATING NORMALLY AT THIS TIME. LEFT INFORMATION ON SILVER MEMBERSHIP.
Found the frozen unit, need to come back another time.
Found evaporator coil covered in slime and TXV bulb had come loose reattach TXV re insulated TXV clean evaporator coil in place and it is Cooling and draining at this time
Found bad capacitor replace capacitor unit working properly at this time
FLUSHED DRAIN LINE AND PAN. UNIT COOLING NORMALLY AT THIS TIME. WILL RETURN TO REPIPE DRAIN
Quoted 510.00 evergreen module unit down homeowner needs to know if part is available tuesday morning they have to leave tuesday