I will call again when you are needed. thank you ! Carl
I have nothing but good things to say about this company. I have used them several times over the past number of years and they have always been exceptionally responsive and reasonably priced. This was put to the test this past weekend. Our air conditioning went out at a house we had guests at about 8:00 pm on a Saturday night. We called their emergency number and they had someone at our house in about 30 mins on a Saturday night. Unable to fix it that night because they needed a new pump, they were back early the following Sunday morning to complete the repairs. Because of them our guests’ weekend was saved from being ruined. This company has great customer service and highly qualified technicians. Highly recommend them. They are the ONLY air conditioning company we use in the Crystal River area and they have certainly earned our loyalty.
The tech arrived within 2 hours of my call, i could not believe it. The problem with our HVAC unit was diagnosed very quickly, repaired and with professionalism. Can't thank them enough.
INCLUDES SILVER MEMBERSHIP GUARANTEED SERVICE 7AM-7PM AND 1 YEARLY MAINTENANCE. 30%OFF ALL PARTS AND LABOR. Replace blown dual run capacitor. Also washed off condenser coil from grass clippings. Unit is operating at this time. Left pricing for new equipment. Customer purchase silver contract
Mini split is a 12000 BTU unit on Cottage on back of the property for the main home. System had H3 error code. According to literature that is compressor overload. Tested compressor .50ohms on each leg of compressor . Was able to determine that compressor overload protector switch was broken on top of compressor. Bypass switch temporarily office will call for availability and check for warranty
Outdoor Motor cycling needs motor and dual capacitor information into parts to quote possible part warranties
Customer still concerned that system is running longer than normal. Ran and checked entire system. Pressures are good 350 head and 130 suction 11 degrees superheat and 14 degrees subcooling. I went ahead and clean condenser and evaporator coil. Fired unit backup and noticed that the outdoor fan will change in Pitch. Also noticed that outdoor fan motor will change amp drawers when the pitch changes. Outdoor fan rated at 1.9 amps. As fan changes pitch amp draw goes from 1.7 to 1.2. Also head pressure will rise as this is occurring. Voltage into system does not change. Ordered new fan motor and blade
REPAIR SUPPLY DUCT AT SUPPLY FLOOR BOX. ALSO RE ROUT 12" SUPPLY AND REPLACE GALVANIZED Y. TO ELIMINATE HARD 90Â°TURN. Air flow throughout home is very good.
Found system off on float switch. Flush drain line and pan added drain treatment system is drain and operating normally at this time also flushed second unit drain line
Checked under mobile ductwork check good cool feeling coming from Bad falling down moisture barrier due to age and condition instruct the customer
CHECKED SYSTEM. UNIT IS OPERATING NORMALLY AT THIS TIME
Found compressor off on overload. Dual run capacitor was weak. Cool compressor and replace capacitor system is operating normally at this time
Check unit system has a 20 degree split and is running very hard 98 degrees outside. Replace dual run capacitor. Rated 70 microfarads + 10 microfarad was reading 70 + 7. Outdoor fan motor amp draw was not high. Replace capacitor head pressure drop slightly system is Cooling and draining fine at this time
Sound system running with 33 degrees subcooling removed 2 lb of puron system is draining better and quieter on shut off and start up
Left price for new unit on bunkhouse
Outdoor fan not running, Found open Dual run Cap, Replaced capacitor, Tested System, Up and Cooling Thank You
Replace fan board on a 2.5 ton rheem
MECHANICALLY CLEANED INDOOR AND OUTDOOR UNIT. FLUSHED DRAIN LINE AND PAN. ADDED DRAIN TREATMENT. VERIFIED ALL AMP DRAWS AND ELECTRICAL CONNECTIONS. CHECKED ALL REFRIGERANT LEVELS AND TEMPERATURES. REPLACED AIR FILTER AND UV BULBS.