Very responsive and thorough service
Don was very informative, professional and enlightened me regarding my unit. He also informed me that I had incurred unneeded costs from using my previous AC company, i.e. a new unit installed 8 years ago that was much larger than needed costing me more than needed. Also a duct cleaning by the same company that cost me $299 that also was unneeded. Also this company recommended Aeroseal without even doing an examination of my system and ducts. Don advised me any leak was not serious enough for this process. As a result, I have discontinued my membership in their service club and severed my relationship with them. I will be using Bay Area in the future.
This is An Estimate to Install A New Carrier 16 seer Two Stage Heat Pump.
Service call completed, upon arrival check system and inspector notes, sealed air handler plenum with mastic, the system is not leaking refrigerant, the cooper line just have the chemical reaction with condensation line, the conderser unit armaflex just need replacement but is not affecting the system performance or operations
Ran complete system tune up. Cleaned primary pan first it had build-up and was tripping float switch. Cleaned drain and coils. Flushed and treated drain and coils. System is working within factory specifications.
Finished gas line connection and tested new furnace. System now ready for inspection. Parts used. 2. Half inch steel elbows 1. Half inch steel coupling 1. 12 inch length of half in steel pipe 1. 10 inch length of half inch steel pipe 1. 8 inch length of half inch steel pipe.
System maintenance on heatpump system One of two system.
System maintenance on heatpump system .
5 ton straight cool with gas
Found system low on 410a refrigerant. Leak searched system and found leak in evaporator coil. Evaporator coil, horizontal drain pan, tx valve and filter drier will need to be replaced. Cost to replace evaporator coil $3907. Custmer is going with new system instead. Install date October 25.
Found x13 blower motor module shorted and causing motor to run continuously regardless of thermostat setting. Replaced motor with Evergreen replacement motor. Tested new motor.
Recovered puron and replaced filter drier and factory evaporator coil. Leak tested and evacuated system. Recharged with 410a Restarted and tested cooling Coil. CAPF4961C6 Collected check for job
Installed temp unit until new install. Charged $500 that will be deducted from new system.
5 ton straight cool with gas. Found internal failure on compressor. Compressor still functions but is loud and likely to fail completely in the near future. Quoted for new system. Current system is not repairable.
Found the system low on 410a. Also found dye coming from the drain line which leads to believe that the leak is in the evaporator coil. Need to have the office check the warranty then give option for coil replacement.
Found that the evaporator coil is impacted. The system is 13 years old. I wouldn't recommend pulling and cleaning the evaporator coil as it could cause refrigerant leaks. Gave an estimate for a new coil or system replacement.
Customer want an estimate on a new compressor and options on replacing the system. Customer wasn't aware of a service fee today.