Technitian was pleasant and professional
Checked system in attic system draining correctly. Coils are in good shape for the age of equipment.
Found od fan wire not connected to capacitor. Coils are clean and draining water properly.
Yearly maintenance on a 3 ton carrier package heat pump. For o e of our many valuable contract customers.
Prepare for a ton Goodman package unit one of our many valuable customers and morriston Florida
Replace indoor blower module on a 4-ton Bryant packaged heat pump for one of our many valuable customers in Morriston Florida
Replaced defrost board in Bryant heat pump
Ac repair replaced board defroster
Repair electric heat on a four-ton Nordyne package heat pump for one of our many valuable customers in levy County Florida
Ac repair annual checkup
Replace indoor blower motor on a 4-ton Nordyne package unit for one of our many valuable customers in Marion County
Perform yearly maintenance for one of her many warranty customers in Morriston Florida