Checked operation of unit, capacitor tested good. Fan motor drwing correct amps. Fan motor did not heat up during visit. Unit is running normally at this time.
Checked operation of unit, found dirty filter as well as unit needed tune up. No problems found. Unit is running normally at this time.
Did a 1st Start for New System, Cooling and Draining Water, Needs Outdoor breaker Replaced to a 30 ITE
Ac repair 5 ton carrier package unit contactor and capacitor
Testing check for ton Carrier split system for one of our many valuable customers in Williston Florida
Yearly checkup on one of our many valuable warranty customers.