The technician seemed very knowledgeable and competent. We were very pleased with the amount of time he spent and the feed back he gave. We were very impressed that he was not rushed and was very thorough.
Called and received same day service. Jeff Myers was my service provider and did a fantastic job. He was very polite and clean. I will recommend him to anyone who has air conditioning issues.
Very friendly and respectful always
Very knowledgeable tech came out, did a check of my system as I thought it was not cooling well last weekend. Nothing was found other than needing freon, once added I did feel the difference. Price was also very nice, will without a dough call them again when service is needed.
Leak search conclusivef of small lea in evaporator Ordering part
Compressors locked up connected signal to find out if unit is still under warranty please have Harry check and call customer with replacement quote for control board and compressor. System is turned off by breaker so we don't do any more damage Pete cannot do this
5 ton unit #1. Clear drain and pan, treat with drain cleaner and tablets. System operating and draining at this time.
Inspect commercial bldg and assess requirements for PM. Spoke with John, informed customer that job would be too much for us .
3.5 ton with 10kw heat strip
Replace evap coil dehydrated system recharged system
Found X13 blower motor shorted and running continuously. 24 volt fuse also open. Seached for short in 24 volt circuit and none other than x13 blower motor. Need to get price on factory replacement Call cell to quote price 352 397 5637
Cleaned out heavy algae and slime from both drain pan and drain line. Added drain tablets and viper pan spray. Restarted and tested drain until water was draining steadily outside. Monitored indoor unit and saw no more water dripping from blower compartment. Vacuumed as much water as possible from bottom of unit. May still drip a little until water dries up
Found board on a/h bad and had heat strip was on with cool. Removed heat out of line. Installed contactor to run fan with cool. No heat now. System is cooling properly now. Mail invoice to customer please.
House was 72 and set at 72Â° when I arrived. Customer showed me a picture showing in the heat of the day it was 77Â° . Coil is clean but, charges are off a little. Trying to find cause. TXV bulb was not completely covered. Found problem . Inspection of duct I found no problems. Thought I did but it was insulation hanging down. Have good air flow. Need to order and replace TXV 6/11/21 Replaced TXV and dryer. Vacuumed down system and recharged system to factory specifications. After installing new TXV and charging I found that compressor has weak valves and not cooling properly. Pressure is running at 192 suction and 296 head. Need to replace compressor on system. 6/12/21 Installed new compressor, vacuumed down and recharged to factory specifications. Ran system diagnostic and technical data System is now working properly. Everything within factory specifications.
Annual maintenance System was noted as low refrigerant added refrigerant to modest charge Leak search needed
Annual maintenance All functions and operations were normal and within parameters Collecting for 2 invoices
Upon the pan that coil sits in was blocked causing water to back up and drip into plenum. Then staining ceiling. I vacuumed drainline and pan multiple times. I flushed drainline multiple times with dawn. It is cooling and draining at this time.
upon arrival the system was shutting down do to high pressure. I noticed system had dirty coils. I decided that the only way to actually resolve the problem was turn call into a tuneup. I checked refrigerant pressures and cleaned both coils. I washed off unit and chevked amp draws. It is now cooling without shutting down on high pressure. Homeowner knows it it getting old and would like to make it through this summer before replacing.
Up stairs system. Found system low on refrigerant. Leak searched system and found leak in evaporator coil. Coil will need to be replaced to correct this problem. Cost is pending. Added no refrigerant today