Would not help Bay Area for me to give my opinion. Was told one thing and did not deliver services as promised until I made a phone call to find out why. The left hand doesn’t know what the right hand is doing. My neighbor had a similar experience.
We had Giovani come out. He was great as always
W were very pleased with the job that Giovani & Sal did on taking out the old unit and installing the new unit. Have used your service before and will continue to use you company if needed and recommend you to all our friends.
Service tech is as very honest, informative, and cared about his customers. He explained that our service call checked out good with nothing but honest and good things to say while giving reputable advice for future visits. No pressure felt.
Great service by Pete Costanzo. He goes above and beyond and answers all our questions regarding our AC unit.
He was very knowledgeable and I appreciated the phone call.
System was low on Refrigerant R22 . Explained to customer this was the only time I could add R22 . If it's to leak out then it's time for new system. Charged System to proper level with one and a half pounds. 70/225 . Coils are clean system is well maintained and customer understands that these systems are phased out.
Customer wants scheduled for tomorrow. He felt bad that it was getting so late.
upon arrival the homeowner said the system would not shutoff when hitting set point. He had to trip breaker. I had him start system and the condenser was making acloud noise. I removed panel and then touched suction line and it was trying to heat and cool. The the compressor sounded like it was running backwards and after removing panel the contactor was pulling in and out very fast. Then compressor shutdown. I pulled disconnect and wire off of contactor o stop the chatters. I tested voltage to all low voltage wires. I had 24 volts to all but yellow. I had 14 volts. I went to air handler and checked and was the same.. I removed core stat and jumped red and yellow together and tested. I had 24 volts. I removed core and I installed temp too tech stat and it is now cooling. I ordered new core stat.
Completed tune up evap rusted compressor weak. Quoted new system
Complete tune up
No cool. Replaced dual capacitor and spade fuse. System operating at this time. Warranty, ordered replacement bulb for Reme Halo.
upon arrival I opened up panel and all the electrical components were cover in ants. I sprayed to remove as many as I could. I used nitrogen to blow them out. Then I found contactor shorted. I replaced contactor and is now cooling.
Cap change out
Found drain line separated where it comes down wall in garage. Repaired and cleaned up. Ran complete system tune up. Cleaned coils and drain. Flushed and treated. System working within factory specifications. Had to pressure wash coil and pan to get out drain line slime.
Need to return and reinstall turning vanes at same time remove suction line drier. Test for acid and brake in 1 1/4" pipe back in place of drier. Note: Talked with Dale about turning vanes . Two people
Compressor is about to lock up. Amps are close to locked rotor amps. Needs new Compressor. 10 ton system need a 7/8" liquid line dryer with valve ports. Compressor is running 10 amps . Information late is completely covered. Not sure how much 410A system holds. Need to look that up before giving price on recharge of system. LRA is 35.5 and compressor is at 28.3 rla 3 phase system. Not running in reverse. I checked that first thing. 10/8/21 Replaced Compressor and installed liquid line drier and suction line drier. Suction line drier to be removed at a later date. To be scheduled. Line drier are not listed so took pictures of part numbers . Leak checked system with nitrogen and then vacuumed down to 241 microns. System now working properly 1" static pressure Put in compressor numbers can't add to materials. Not listed.
Old York system is out of refrigerant (0 pressure); appears system dares to 88 or 87, System not worth pursuing repairs, serves North end of sanctuary. Access thru ceiling of Ladies room 2nd system for kitchen and adjacent bathroos across hallway has failed blower motor. This unit also accessed thru Ladies room ceiling Office to quote motor
Removed blower houseing to confirm diognostics, blower motor drops out/in rapidly Part order request
Both o.d fan motors on unit #6 are not working compressor is really loud also I.d blower motor belt is very wore out .. checked capacitor they seem to be good... 3 faze unit I currently do not have a meter for.. no model or serial #
Found water leaking at the rubber tubing and copper connection. Going to order a new pump and redo those connections to stop the water dripping. Customer is upset over the damages to the door. Took photos and sent to management. Completed the repair and fixed the pin hole leak within the 3/8" copper line.