I am very happy with this service, especially since it was necessary on a holiday weekend. Mike identified the problem immediately and replaced the appropriate parts in a timely manner. He was friendly, professional and restored my A/C. I am so thankful!!!
Shane Killeen was very thorough. He explained everything he did and he was very friendly.
Told me of problems and why and made sure I understood it
I appreciate your company’s commitment to service and their customers. Shane showed professionalism and knowledge in his service performance. He is truly an asset to this company. Thank you BayArea.
Bay Area has been our A/C service repair company since we moved here 3 years ago. Always great and efficient service. Shane was here today and was both quite knowledgable and quick to fix the problem. Another COOL day in our forecast. Thanks Bay Area.
Fast, friendly and top notch service. Technician went above and beyond to inspect and service my system.
Our AC went out on the holiday. I called the next business day and they immediately got us on the schedule for service. They told me the name of the tech and approx time of arrival the tech called when he was 15 minutes out. He was reliable and truthfull A big plus for older people. Highly recommend Bay area
A/C Service on Carrier 2 ton air conditioner. Performed preventive maintenance.
Annual check-up 3 ton Payne heat pump
Annual check-up 3 -ton Carrier Infinity
Air conditioning repair 3 ton Carrier heat pump drain line drain pan
Dunnellon Replaced condenser contactor on TRANE ac unit
Replace dual run capacitor on a 3-ton Carrier split heat pump for one of her many valuable customers in Citrus Springs Florida
Annual check-up 3 ton Rheem heat pump
Annual check-up 3-ton Carrier heat pump
Yearly maintenance on a 3-ton Carrier split heat pump for one of her many valuable customers in Citrus Springs Florida
Dunnellon Cleaned up clogged drain on Carrier ac system.
And Your Service carrier to speed performance heat pump
AC repair 3 ton Rheem heat pump x13 module
Compressor not starting replaced bad / overheated capacitor. System started but unit needs annual service to operate at Peak efficiency
Install 3-way tee and flush drain period continuing problem from few months back
Inspected many split for foul smell clean coils and adjust drain. Feel smell is coming from elsewhere