You have my business!
Quick clean great care
They were Polite, friendly, thorough and knew there stuff, I’m so glad I called Bay Area A/C
I call realtor and discussed settings for ac. It is my recommendation that the system should not be any lower than 72. Lower temperature settings may cause coul to ice up and ruin coil. When leaving for the day the setting should be raised to 74 to 76 degrees. To large of a temp setting will cause system to run for long periods of time to achieve set point.
Checked over the air flow and gave an estimate to fix the issues.
Upon arrival I had some trouble with gate codes. Homeowner had them changed thinking we were already here. Then I checked filter doors and one was broken and the i repaired. Then I found breaker off. It was not tripped but off. I turned it on and the condenser started. I set stat to 76. I checked drainline and was cleared. I ordered part for filter door. Will collect when filter door is repaired.
Upon arrival i found no refrigerant in system. I pressurized system and found capillary tube covered in some kind of corrosion. The pan was full of it. Then i noticed some kind of big pan treatment on top of coil. When it melted from condensation it ran down coil and built up in corners of pan and looks like it eroded capillary tube. I quoted coil and discussed with homeowner on multiple phone calls. I could not collect because she had to hang up for important call.
Upon arrival temperature was in low forties. Homeowner did not want pressures or equipment tested at this time do to not getting accurate readings. Wants a tech to return when temps are above 70. I did wax outdoor unit. I cleaned both coils and flushed drainline multiple times with dawn. I did jot do technical data.
Maintenance completed, drain and flush condensation line , advised client to replace air filter regularly, check electrical components and refrigerant pressure, clean condenser coil and evap coil, during maintenance found the air handle breaker wasn't engaging to the on position, open panel or the main breakers and found a defective 60 amp cuttler hammer, replaced under the 1st year of labor warranty, advised client for future reference, main breaker , thermostat wires and condensation line aren't covered by the Part and labor warranty, tested equipment operations, all systems vital are good at this time
Found open 24 volt circuit inside indoor unit at moles plug. Correcred open circuit and restarted cooling. Warranty.
Replaced shorted dual run capacitor. Restarted and tested cooling and checked puron level. Made sure drain was clear. Parts are still warranty until 7,29,21
Replace the indoor fan motor on Carrier Infinity greenspeed heat pump air conditioning system in Dade City
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 4 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 3 TON PAYNE HEAT PUMP SYSTEM
Installed new carrier programmable thermostat on Carrier Comfort straight cool air conditioning system in Dade City
customer just purchased a new carrier Comfort heat pump air conditioning system with complete ductwork replacement in Dade City
Left a quote for new ductwork and heat pump Carrier air conditioning system in Dade City