Quick clean great care
They were Polite, friendly, thorough and knew there stuff, I’m so glad I called Bay Area A/C
Upon arrival i found no refrigerant in system. I pressurized system and found capillary tube covered in some kind of corrosion. The pan was full of it. Then i noticed some kind of big pan treatment on top of coil. When it melted from condensation it ran down coil and built up in corners of pan and looks like it eroded capillary tube. I quoted coil and discussed with homeowner on multiple phone calls. I could not collect because she had to hang up for important call.
Upon arrival temperature was in low forties. Homeowner did not want pressures or equipment tested at this time do to not getting accurate readings. Wants a tech to return when temps are above 70. I did wax outdoor unit. I cleaned both coils and flushed drainline multiple times with dawn. I did jot do technical data.
Maintenance completed, drain and flush condensation line , advised client to replace air filter regularly, check electrical components and refrigerant pressure, clean condenser coil and evap coil, during maintenance found the air handle breaker wasn't engaging to the on position, open panel or the main breakers and found a defective 60 amp cuttler hammer, replaced under the 1st year of labor warranty, advised client for future reference, main breaker , thermostat wires and condensation line aren't covered by the Part and labor warranty, tested equipment operations, all systems vital are good at this time
Found open 24 volt circuit inside indoor unit at moles plug. Correcred open circuit and restarted cooling. Warranty.
Replaced shorted dual run capacitor. Restarted and tested cooling and checked puron level. Made sure drain was clear. Parts are still warranty until 7,29,21
Replace the indoor fan motor on Carrier Infinity greenspeed heat pump air conditioning system in Dade City
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 4 TON CARRIER INFINITY GREENSPEED HEAT PUMP SYSTEM
ANNUAL AC MAINTENANCE TUNE UP AND CLEANING ON A 3 TON PAYNE HEAT PUMP SYSTEM
Installed new carrier programmable thermostat on Carrier Comfort straight cool air conditioning system in Dade City
customer just purchased a new carrier Comfort heat pump air conditioning system with complete ductwork replacement in Dade City
Left a quote for new ductwork and heat pump Carrier air conditioning system in Dade City
AC SERVICE REPAIR ON A 3 TON GOODMAN STRAIGHT COOL SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A 4 TON CARRIER PERFORMANCE HEAT PUMP SYSTEM. ORDERED BLOWER MOTOR AND MODULE.
Replace outdoor fan motor carrier system