Found two issues that prior companies never fixed.
Business like and explained what he found.
Efficient and effective
Very knowledgeable and very polite
appreciated the service
Problem was my new “nest” thermostat settings. Steve was very helpful in figuring why my emergency heat kept coming on for no reason. Working with nest help line made adjustments which solved the problem. Thank Bay Area and Steve for great job.
customer will call back when Dry's out
All labor and material is included 1 year parts and labor warranty on all work NO WARRANTY ON THE EXISTING TRANE SYSTEM.
Systems locked rotor amps were 113.8/150. All other system functions are normal. Added a hard start to do initial amp draw, speed it to 48/150. Washed condensing coil to improve efficiency and extent lifespan of unit. Unit is cooling and running fine.
System had a weak capacitor. Change capacitor out in unit fired right up. Compressor amp draw is 10 / 21.8 and the fan amp draw is 1.2 / 1.4. Unit is running Cooling and draining fine
System had a clogged drain line. Cleared the clog and treated the drain pan with an antimicrobial agent. Units coils are relatively dirty. Inform customer that I recommend calling the office and getting a checkup. Unit is running fooling and draining fine.
Unit at a capacitor that was weak on the fan side causing the fan to overheat and possibly shut off not allowing heat exchange causing the compressor to shut off and not provide cooling for the customer. Customer has a 10-year part warranty from carrier. Change out the capacitor and tested the unit to ensure everything was working fine. Unit is working normally.
This is An Estimate to Install A New Carrier 14 seer Package Unit Straight Cool with Elec Heat
CARRIER 2 STAGE HEAT PUMP WITH WIFI THERMOSTAT AND VARIABLE AIR FLOW. 10-YEAR PARTS AND LABOR WARRANTY. COMPLETE SYSTEM
System had a bad blower module. Ran to shop to pick up replacement. Installed new module and unit is Cooling and running fine.
Cleaned indoor and outdoor coils as well as drain line and treated drain pan with antimicrobial agent. Checked all electrical connections and amp draws as well as refrigerant circuit pressures and temperatures. Unit is working fine.
System had a bad condensing fan motor. Changed and added new capacitor. Fan amp draw is 1.14/2 and compressor is 9.8/14.7. Unit is cooling fine.
System operating normally. Charge looks good, superheat and subcool do as well. Compressor amp draw 10.1/16 and condensing fan pulling 1.3/1.5. System is draining well and the drain pan is clean. Replaced failed float switch. Unit is doing fine at this time.
System was freezing up based on what customer inform me of. Has not run AC in several days. Verified air flow was good in that there was no crushed duct work underneath trailer. System pressure was extremely low so charge system with 1 lb of R22. Inform customer that due to it being a package unit it probably has a leak but hoping that it's a slow leak. Unit is working fine.
Mini split low on charge. We were out here a couple of months ago for the same problem. Customer knows there's a leak in the coil. Will be replacing mini split themselves here soon and just need this to get by until installation possible. Charged 2 lbs r410a into system until suction pressure was 125. Unit is operating normally.