I purchased a new system approximately 3 years ago and choose to have a preventative maintenance done annually just to help prevent any unforeseen issues. Everyone that I have spoken with whether at the office or those employees coming out to do the work have always been very courteous, professional, efficient and helpful. I don’t think I could have made a better choice. I would definitely recommend them to anyone!
Very satisfied with company and all personnel
Bay Area...you have nicest and knowledgeable techs....thank you!!
He did a great job.
Always prompt and knowledgeable
Maintenance completed, drain and flush condensation, cleaned washable air filter, clean evap coil and conderser coil, checked system electrical components and operations, system vitals are good at this time
Ran complete system tune up. Cleaned system and treated drain and evaporator coil. Static is good charges and electric with one exception. Capacitor is failing. Its at 40 mfd and should be 45 mfd but no less than 42 mfd. Explained to customer and gave a price.
maintenance completed, check and tested electrical components and refrigerant pressure, removed top cover of package unit, clean evap coil and conderser coil, advised client to replace air filter regularly, system is 3 years old, all systems vital are good at this time
maintenance completed, removed top cover on package unit, clean condenser coil and evap coil, removed debris fron drain pan and cleaned with drain pan cleaners, re attached insulation of the to cover that insulated the evap coil section, check and tested electrical components, system is operating within manufacturer specifications at this time , recommended client to replace air filter regularly, client pay with cash the maintenance service
Maintenance completed, checked refrigerant pressure and electrical components, clean evap coil and conderser coil, remove debris on the package unit, system is 12 years old, all systems vital are good at this time
Maintenance completed, drain and flush condensation line, clean with evap coil and conderser coil, check electrical components and refrigerant pressure, during the maintenance notice fan blade it seems unbalanced, there's moderate vibration on the motor, advised client system condition, client stated that system has a miodew smell when system in operation, coils look clean advised to replace air filter regularly and if problems persist look into installing a u.v light system or air Purifier, sending u.v quote on the email on file
Checked over the thermostat settings and found that it was wired wrong. Installed the customers new thermostat and tested the thermostats operation. Heating and cooling both came on.
Service call completed, client concerns about condensation on the unit in heat mode ,explained that this is happening when system is becoming to the defrost cycle, and the loud noise and are normal when this cycle is being activated when the outdoor coil are too cold , advised client system condition and operation recommended to replacd air filter regularly
3 TON CARRIER 14 SEER HEAT PUMP WITH WIFI THERMOSTAT AND 10 YEAR PART AND LABOR WARRANTY
This is An Estimate to Install A New Carrier 18 seer Five Stage Heat Pump. With A 10 Year Part and Labor Warranty.
New Tstat wire,
Service call completed, thermostat has a factory comfort setting, clien was able to delete those setting and changed to their comfort setting, tested equipment, all systems vital are good at this time
Maintenance completed, drain and flush condensation line, check air filter and recommended to replace filter every 3-6 months, clean evap coil and conderser coil, check electrical components and refrigerant pressure, system has 2 u.v system, one of the bulb need replacement, bulb quote is sedn on the email on file
Found thermostat not working properly. Installed new and tested. System now working properly . Stat m# TCNHP01A s# 1920M124835
Upon arrival i removed old stat and back plate and installed both new. I setup stat and tested. I longer have 16 volt bleed back on y2. I cycled system and fan shut off at the end of it.