We have used Bay Area for over 10 years and find their techs to be knowledgeable and friendly workers who don't mind having the home owner watch them do their job. We will continue our contract for another year.
Bay Area tech was able to come right over since our air went out late afternoon. He was very knowledgeable & fixed the problem. We are in our late 70 's & appreciate prompt courteous service which was provided due to our medical problems.
David did a wonderful job .Been with Bay Area for 17 years now .H e is the best.
Our thermostat had a system failure error message. This was a Saturday PM. When I called Rob said he could come ought within the hour. Since it was dark I asked if he’d like to come in th AM so he could see what he was doing outside. He was more than happy to come right away but appreciated being able to come in the AM. He is very much an asset to Bay Area AC
Very good response.
Bay area is the best. Every one was friendly and professional. The service was performed in a timely manner. I am very pleased and satisfied. Thank you.
David really does a excellent job .I AM SO HAPPY WHEN I GET HIM.
Annual service contract maintenance tune up and cleaning on a 4 ton TRANE heat pump system.
Annual ac maintenance tune up and cleaning on a 3 ton Carrier heat pump package unit.
Annual service Carrier infinity heat pump
Annual service contract maintenance tune up and cleaning on a 3 ton Carrier heat pump system.
Replaced reversing valve on York heat pump
AC SERVICE REPAIR ON A 4 TON CARRIER INFINITY HEAT PUMP SYSTEM. Raised condenser unit two blocks high.
Air conditioning repair 4 ton Carrier heat pump thermostat
Replace indoor blower on a 4-ton Carrier Infinity heat pump for one of our many valuable warranty customers in Homosassa Florida
Replace module on blower motor on Carrier air handler
Checkup and cleaning on Tempstar heat pump. Quoted ductwork
Repair wire reset breaker Carrier Infinity heat pump
AC SERVICE REPAIR ON A 4 TON Lennox heat pump system. System was down do to power management.
AC SERVICE REPAIR ON A 2 TON RHEEM HEAT PUMP SYSTEM. REPLACED CAPACITOR.
AC SERVICE REPAIR ON A 3 TON RHEEM HEAT PUMP SYSTEM. CLEARED CONDENSATION DRAIN LINE.
AC SERVICE REPAIR ON A 4 TON CARRIER PERFORMANCE HEAT PUMP SYSTEM. REPLACED CAPACITOR.